Question about Plumbing
Grundfos 32-60/4 a f a bube heating pump. i need to know whether the internal overload is an adjustable type or a fixed set point. there are some white wires under the wiring box and i am not sure whether this is the overload or not as i dont have a booklet with it
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Thanks for the response, to be more specific, the nine pin connector was damaged, but I was able to connect the wires back to main unit panel. I am ready to hook to the hunter thermostat and do not know which wires to connect to. This is my problem and I do not want to short something out. Hope this helps, I want to get it installed again. Thanks again for caring....Jerry
Posted on Aug 16, 2008
I don't know if this will be helpful or not, but I just installed a new Honeywell and the Honeywell customer service guy helped me get the wires done correctly. The number is 800-468-1502.
Posted on Jan 05, 2009
Unfortunately, the wiring diagrams for heat pumps are not so easy to come up with. The outdoor unit will have its own diagram, but may not include the indoor air handler and will probably not include the thermostat. That said, the orange wire is commonly run from the thermostat to the reversing valve in the outdoor unit. This wire is usually not connected to the indoor airhandler. The orange wire is usually used in a unit that has the reversing valve energized in cool. Ruud, however has its reversing valve energized in heat. Probably not useful but maybe helpful
Posted on Mar 26, 2009
green to srcew on the motor. this is ground.,
Black on T1
Red on T2
If the rotation is going the wrong way, simply switch the black to T2
Red to T1.
Check this before you couple it to the pump..
Posted on Jun 03, 2009
Tips for a great answer:
Feb 19, 2017 | Grundfos Plumbing
Aug 02, 2014 | Grundfos Pumps Grundfos Redi-Flo2 Electric...
Dec 01, 2013 | Plumbing
Oct 13, 2013 | Grundfos Pumps UPS15-58FC
Jul 06, 2011 | Grundfos 505474 24-Hour Progammable...
Nov 20, 2010 | Grundfos The UP1510B5ATLC 125th HP 1...
Sep 15, 2010 | Grundfos RCP-96 Recirculation Pump for...
102 people viewed this question
Usually answered in minutes!