Question about Carrier 38CKC042 Air Conditioner
I put the indoor unit on hot and you hear the outside unit start up, starts to blow , then it cuts out within a minute to 2 minutes. What could be the problem. Many thanks
There is a low voltage wiring problem. Make sure your t-stat wire is in the correct positions and that you have not removed the jumper wire at the t-stat. There should only be 2 control wires leaving the airhandler and going to the condenser unit outside. Unless it is a heatpump. One wire goes to common and the other goes to the Y terminal. W terminal is for heat. The unit will cut off if you have the unit calling for heat and cool at the same time.
Posted on Jan 05, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 31, 2015 | Heating & Cooling
Apr 07, 2015 | Goodman Heating & Cooling
Jun 22, 2014 | Carrier 3 Ton Infinity Puron A/c outside...
Jun 26, 2011 | Heating & Cooling
Aug 15, 2010 | Carrier 38CKC042 Air Conditioner
Mar 02, 2010 | Heating & Cooling
Aug 09, 2009 | Carrier Heating & Cooling
Apr 15, 2009 | Fujitsu 18R1 Air Conditioner
Sep 03, 2007 | Carrier 38CKC036 Air Conditioner
65 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: