Question about Coleman Heating & Cooling
Posted by Anonymous on
WHERE CAN I BUY REPLACEMENTS PARTS FOR THE SAME MODEL # G8T10012UHB11A
Posted on Dec 10, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
you probably have a cracked heat exchanger which is causing the rollout switches to trip.even the tiniest of cracks will cause the fan to blow the flame back into the unit and cause them to trip. check the heat exchanger for even the tiniest of cracks if so replace it. and be sure to have a carbon monoxide alarm in your home.
Posted on Oct 30, 2008
ok this is going to sound funny but it seems as though the polarity is reversed going into your furnance. to correct this proiblem you first need to unplug the unit and where the cord goes into the furnance at that connection disconnect the two wires. Once theses are disconnected switch the wires .All you are doing is reversing the way the electricity flows into the circut board. I would wager that is the problem
Posted on Apr 16, 2009
Hi, this motor is the inducer motor, which is the first thing to start on a call for heat. Everything seems to be going through its sequence of operation just fine, but then shutting down on a safety. Look on the panel for a chart that should tell you by the number of flashes and color of the leds what is wrong. It is locking out for some reason, could be several of many. Next to the pilot, you will have a flame sensor. The metal tip sets in the pilot flame. When they get dirty, they will cause the furnace to do just as you say, run and then lock out. You can take a piece of sanding cloth and sand the metal tip on this flame sensor. If this is the problem, it will start and stay running. Also, look for this chart I have told you about, as it is there to help you locate which safety is giving you the problem. My bet is the flame sensor. Please keep me posted, and rate me on my help to you. The flame sensor also has a electrical lead that is attached to it going to the board, so you will see it.
A/C, & Heating Contractor
Posted on Jan 06, 2011
Tips for a great answer:
Jan 23, 2016 | Heating & Cooling
Oct 03, 2015 | Cars & Trucks
Nov 12, 2013 | Heating & Cooling
Nov 06, 2012 | Coleman Heating & Cooling
Oct 18, 2011 | Goodman GMS90703BXA Heater
Dec 02, 2010 | Heating & Cooling
EACH OF THE FOLLOWING STATUS CODES IS A TWO DIGIT NUMBER WITH THE FIRST
DIGIT DETERMINED BY THE NUMBER OF SHORT FLASHES AND THE SECOND DIGIT BY
THE NUMBER OF LONG FLASHES.
11 NO PREVIOUS CODE - Stored status code is erased automatically after 72
hours. On RED LED boards stored status codes can also be erased when power
(115 VAC or 24 VAC) to control is interrupted.
12 BLOWER ON AFTER POWER UP (115 VAC or 24 VAC) -Blower runs for 90
seconds, if unit is powered up during a call for heat (R-W closed) or R-W opens
during blower on-delay.
13 LIMIT CIRCUIT LOCKOUT - Lockout occurs if the limit or flame rollout switch is
open longer than 3 minutes.
- Control will auto reset after three hours. - Refer to #33.
14 IGNITION LOCKOUT - Control will auto-reset after three hours. Refer to #34.
21 GAS HEATING LOCKOUT - Control will NOT auto reset.
Check for: - Mis-wired gas valve -Defective control (valve relay)
22 ABNORMAL FLAME-PROVING SIGNAL - Flame is proved while gas valve is
de-energized. Inducer will run until fault is cleared. Check for:
- Leaky gas valve - Stuck-open gas valve
23 PRESSURE SWITCH DID NOT OPEN Check for:
- Obstructed pressure tubing. - Pressure switch stuck closed.
24 SECONDARY VOLTAGE FUSE IS OPEN Check for:
- Short circuit in secondary voltage (24VAC) wiring.
31 PRESSURE SWITCH DID NOT CLOSE OR REOPENED - If open longer than
five minutes, inducer shuts off for 15 minutes before retry. Check for:
- Excessive wind - Proper vent sizing - Defective inducer motor
- Low inducer voltage (115VAC) - Defective pressure switch
- Inadequate combustion air supply - Restricted vent
- Disconnected or obstructed pressure tubing
- Low inlet gas pressure (if LGPS used)
If it opens during blower on-delay period, blower will come on for the selected
33 LIMIT CIRCUIT FAULT - Indicates a limit, or flame rollout is open. Blower will
run for 4 minutes or until open switch remakes whichever is longer. If open
longer than 3 minutes, code changes to lockout #13. If open less than 3 minutes
status code #33 continues to flash until blower shuts off. Flame rollout switch
requires manual reset. Check for: - Restricted vent
- Proper vent sizing - Loose blower wheel - Excessive wind
- Dirty filter or restricted duct system.
- Defective blower motor or capacitor. - Defective switch or connections.
- Inadequate combustion air supply (Flame Roll-out Switch open).
34 IGNITION PROVING FAILURE - Control will try three more times before lockout
#14 occurs. If flame signal lost during blower on-delay period, blower will come
on for the selected blower off-delay. Check for: - Control ground continuity
- Flame sensor must not be grounded
- Oxide buildup on flame sensor (clean with fine steel wool).
- Proper flame sense microamps (.5 microamps D.C. min., 4.0 - 6.0 nominal).
- Gas valve defective or gas valve turned off - Manual valve shut-off
- Defective Hot Surface Ignitor
- Low inlet gas pressure
- Inadequate flame carryover or rough ignition
- Green/Yellow wire MUST be connected to furnace sheet metal
45 CONTROL CIRCUITRY LOCKOUT Auto-reset after one hour lockout due to;
- Gas valve relay stuck open - Flame sense circuit failure
- Software check error
Reset power to clear lockout. Replace control if status code repeats.
If status code recall is needed, briefly remove then reconnect one main limit wire to display
stored status code. On RED LED boards do not remove power or blower door before initiating
status code recall. After one status code recall is completed component test will occur.
Thanks for Choosing FixYa.
Oct 05, 2010 | Heating & Cooling
Dec 12, 2009 | Heating & Cooling
Dec 16, 2008 | Goodman Heating & Cooling
Oct 25, 2008 | Heating & Cooling
729 people viewed this question
Usually answered in minutes!