Question about LG LSU246HV Ductless Outdoor Heat Pump 14.7 SEER 24,000 BTU 2 Ton
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
CH46 Outdoor unit suction sensor fault. Disconnect from PCB and measure resistance. 10 kOhm at 10°C and 4 kOhm at 30°C. If OK replace PCB, if not replace sensor. Helpful?
Posted on Dec 30, 2010
Tips for a great answer:
Sep 01, 2015 | LG Heating & Cooling
May 11, 2011 | Sharp AR-5316 Advanced Digital Imager...
Jan 21, 2011 | LG LA185HV Split System Air Conditioner
Dec 22, 2010 | Sharp AR-5316 Advanced Digital Imager...
Nov 23, 2010 | Sharp AR-5316 Advanced Digital Imager...
Apr 30, 2009 | LG Art Cool LA181CNW Split System Air...
Mar 03, 2009 | Sharp AL-1641CS Laser Digital Copier
Jan 20, 2009 | Sharp AL 1631 Copier
40 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: