Question about Heating & Cooling
The furnace is blowing the circuit breaker. How do I go about trying to find the problem?
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Carrier air conditioner
Sounds like you either blew a transformer, have a bad circuit breaker or blew the main fuse in the outside disconnect. If the indoor unit is still blowing air (no matter what temperature) start looking at the power supply to the outdoor unit. From the circuit breaker, the power will go to a small box located within a few feet from the outside unit. This box will have either a lever on the side or you will be able to open the box and pull out the fuses. From this box the power goes to the condensor. The first thing you should do is to turn off the breaker to the outside unit. Flip it back on and if you have a call for cooling, after about 3 minutes the outdoor unit should start. If it does not, shut off power again to the unit by switching off the breaker, go outside and pull out the fuses in the disconnect box. Using a multi meter, check for continuity thru the fuses. If you have continuity, call your technician. If one or both fuses show no sign of continuity, replace the fuse(s). Make sure that the thermostat is working and sending a signal to the indoor air handler. You may be able to check this by turning the fan switch to "Fan" and see if the blower turns on. You may just have a bad thermostst. Caution should be used anytime you are near electrical components. If you do not have the skill-set required to test electrical equipment, leave it to a proffessional.
Posted on Sep 04, 2007
Hi!!! Does your ac unit work fine?If not check your low voltage problem..You have a low voltage problem check the wire going out to your condensor make sure that they are not touching..Good luck..Check low voltage wires..short in progress..
Posted on Jan 04, 2009
heres the manual for the unit, look at pages 46-47 and theres a trouble shooting ladder schematic that asks what the systums are then gives the solutions for the fix. if you are still having problems you can request to talk to me and I'll be more than happy to help.
Posted on Jan 11, 2009
SOURCE: Code 32 when wind blows
Hi and welcome to Fixya. I believe that the wind is affecting the draft. What I would recommend is to install a cap on the flue that is similar to a weather vane in that it rotates to block the wind from creating a downdraft in the flue. Some times depending on the direction and strength of the wind it will come up over the roof peak and then down the flue. A regular fixed cap may work too. You should be able to purchase one at your local hardware store. Please let me know if this was helpful. Good luck.
Posted on Jan 25, 2009
Could be that the compressor is locked up or either start components are bad..... need to get an AMP gauge and see what the AMP draw is when you hear the compressor try to start which is the click, Hmmmm, click your hearing,
Posted on Jul 07, 2009
Tips for a great answer:
Feb 11, 2014 | Heating & Cooling
Oct 08, 2012 | Heating & Cooling
Jan 20, 2012 | Heating & Cooling
Jul 07, 2010 | Carrier 38CKC036 Air Conditioner
Nov 21, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jun 16, 2009 | Carrier 38CKC042 Air Conditioner
Jan 25, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Dec 31, 2008 | Carrier 38CKC042 Air Conditioner
Nov 28, 2008 | Carrier Heating & Cooling
259 people viewed this question
Usually answered in minutes!