Question about Heating & Cooling
Posted by Anonymous on
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Gas apliances have safety features built into them so you don't blow yourself up. The pilot heats a thermocoupler which tells the gas valve there is a flame, open the main gas to the burner. If you can see the flame area of the pilot look for a round post about 3/16 inch in diamiter. This should be directly in the flame, if not bend the bracket so it is in one side of the pilot flame. The thermocouple is attached to a mounting bracket. This will be held in place by a 1/4 inch hex screw. remove the screw and the capilary tube leading to the gas control valve. Before you do anything, close the main gas supply to the fireplace and disconnect the power to the fan. You may need to semi dismantle the fireplace to get the thermocouple. The gas valve end is a brass 1/4 pipe thread plug. Turn the outer nut and remove without twisting the tube. Reverse this order to install a new one. Besure not to twist the capilary tube, tighten brass nut 1/4 turn past hand tight. Your better heating supply house will have these in stock. Restarting the pilot will take a few tries because the gas was off. Your gas suplier would charge about $75 to fix this. if you don't have the proper tools and it dosen't look pretty stright forward don't do it. You could get dead.
Posted on Dec 02, 2008
Most gas valves have a flame sensor, which is a metal bulb at the end of a wire. The pilot light heats this bulb, and the valve stays open because there's a flame. If the flame has been out, you'll need to hold down the pilot light button for as much as two minutes after lighting the flame to allow the flame to heat the flame sensor up enough to keep supplying gas when you release the button.
Posted on Mar 17, 2010
Tips for a great answer:
Jan 25, 2014 | Procom Dual Fuel Vent-Free Fireplace with...
Jan 28, 2013 | Skytech 3301 Thermostatic Gas Fireplace &...
Jan 21, 2013 | Napoleon 36" Zero Clearance Top/Rear Vent...
Nov 16, 2012 | Grilling
Aug 10, 2011 | Williams 2509612 Ceramic Mid-Size Heater
Jan 07, 2010 | Blue Flame Charmglow 30K BTU Propane Vent...
Dec 11, 2009 | Vermont Casting VCS4017 (NG)
Feb 18, 2018 | Heating & Cooling
227 people viewed this question
Usually answered in minutes!