Question about Flotec Fp4332 1 Hp Convertible Jet Pump ()
We primed the pump continuously but not enough pressure to pull the water through. We changed the voltage to 115 on the pump because we were plugged into a 115volt outlet but still no water pressure.
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
The tank is an air tank, it works like a cushon and accumulator.
Have you reconnceted the pump? If not fill the pipe that goes to the well with water. It should not drain down, there should be a foot valve that prevents the water from running back into the well. So if the foot valve is working it should not take a lot of water to do this.
Pour water into the suction side of the pump until the pump is as full as you can get it, reconnect the pump and start it up. Yes it does need to be primed
Posted on Mar 17, 2009
it might be that the pump is prewired at 230 volt and you are running a 115 power supply to it, if motor just humms and little water comes out this might be your fix
Posted on Apr 01, 2009
if the pump is working correctly, it can either be, need more water to prime it, or something in the well, such as low water, plugged filter, etc....sometimes when you have a system that is intermittently used, it can take 20 or 30 minutes of continuous priming to get it to pull, enough water to maintain the prime.
Posted on Apr 06, 2009
Tips for a great answer:
Jul 29, 2015 | Utilitech 1/2 HP Convertible Jet Pump...
Jul 26, 2015 | Jet Plumbing
May 16, 2015 | Jet Plumbing
Mar 25, 2015 | Utilitech 1-HP Cast Iron Convertible Jet...
Jul 24, 2014 | Utilitech 1-HP Cast Iron Shallow Well Jet...
May 10, 2014 | Utilitech 1/2 HP Convertible Jet Pump...
Dec 01, 2013 | Utilitech 1-HP Convertible Jet Pump...
Sep 24, 2010 | Plumbing
Apr 06, 2009 | Flotec Corrosion Resistant Shallow Well...
May 31, 2013 | Flotec Fp4332 1 Hp Convertible Jet Pump ()
Mar 28, 2011 | Flotec Fp4332 1 Hp Convertible Jet Pump ()
62 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: