Question about Water Heaters
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Check the following:
See if your heater has a pilot gas adjustment valve. It should be on the gas control valve somewhere. Not all heaters have these. It will be a screw on the valve that can be turned.
Make sure the thermocouple sensing bulb is squarely in the pilot flame and also check that the fitting where the other end of the thermocouple connects to the main gas valve is tight.
Check the pilot gas orifice (where the pilot gas comes out) for carbon build up - you may need to remove the pilot gas line and thermocouple assembly to get to this. This problem is pretty common.
Check the gas pressure to the heater. Run the hot water in the dwelling until the hot water heater starts. Check the flame on the main burner and see what color it is - it should be blue with possibly some yellow-tipped flames. If not, there could be a problem with the gas pressure at the heater or venting. If the heater has a gas pressure regulator, it may be out of adjustment or defective.
Finally, and this isn't very common, the pilot light can be extinguished if there is a draft problem, usually associated with an issue with the flue pipe venting system for the heater or another nearby gas consuming appliance.
Posted on Dec 31, 2009
Testimonial: "thank you. will try these suggestions tomorrow. really appreciate it."
SOURCE: need reset code for richmond
I am poting this here hopefully it will help someone else. I have a richmond 40 gallon power vent water heater and it was not working. It was flashing 2-3 on the LED. I used this procedure and it started up..
you can reset the control by unplugging the blower during start up, leave unplugged for at least 5 seconds, plug back in and within 30 seconds cycle temp control from hot to low 6 times.
Posted on Apr 13, 2010
lock out code....turn off unit for 1 minute (unplug) press both arrows and hold for 5-10 sec... then enter L R L L ... R L R R...that should reset it.
Posted on Jul 25, 2010
Tips for a great answer:
Mar 04, 2015 | Water Water Heaters
Sep 14, 2014 | Rheem Richmond 40 Gal LP Gas 6 Year Tall...
Mar 21, 2013 | Audiovox Richmond 6G40-36F 6-Year Tall Gas...
Mar 10, 2013 | Water Heaters
Aug 06, 2012 | Rheem Richmond
Aug 03, 2011 | Audiovox Richmond 6G40-36F 6-Year Tall Gas...
Mar 13, 2011 | Audiovox Richmond 6G40-36F 6-Year Tall Gas...
Aug 11, 2009 | Audiovox Richmond 6G40-36F 6-Year Tall Gas...
Jun 20, 2018 | Water Water Heaters
2,923 people viewed this question
Usually answered in minutes!