Question about Goodman Manufacturing Goodman MSG18HRN1 MSG-18HRN1 Wall Ductless Heat Pump 13 SEER 18,000
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: goodman gph1348m41ac unit is blowing cool air in heat mode with mid 30s ambient outdoor temp. I turn it off then on and will usually blow warm air but this cycle is becoming more repetitive. any expe
A heat pump on the optimal heating day (about 50 degrees ambient) will only deliver approximately 85 degree air as compared to 125 degree air from a fossil fueled furnace. The colder the outdoor air is the less heat there is available to be transferred to the living space. At 30 degrees, the heat transfer capability is getting close to negligible meaning the run cycles will be approaching continuous and eventually as the heat pump along cannot maintain setpoint, the outdoor stat or stats will bring on auxilliary heat in the air handler.
If your ambient temp is below the 'balance point' of the heat pump, the house temp will drop a little lower and most times energize the heat strips through the outdoor t-stat. Your outdoor stat could be set too low for the heat pump to carry the structure all the way down to the balance point so when you turn it off and back on, the lower indoor temp automatically brings on the heat pump plus a heat strip or two, thus the warmer air. Second stage on the stat satisfies due to the heat strip, drops them out of the circuit and the heat pump is left running on first stage heat delivering the perceived cold air.
Your outdoor stat could also be not functioning correctly and not allowing the heaters to come on until the system is turned back on reestablishing the two stage call for heat.
Tons of possibilities and not enough room to list....
Posted on Jan 01, 2015
Tips for a great answer:
Apr 07, 2015 | Goodman Heating & Cooling
Nov 11, 2013 | Goodman Manufacturing Goodman ARUF486016...
Sep 12, 2013 | Goodman Heating & Cooling
Feb 13, 2011 | Heating & Cooling
Dec 11, 2010 | Goodman PHKJ048-1 Air Conditioner
Dec 15, 2009 | Goodman CLQ36AR49 Air Conditioner
Oct 13, 2009 | Goodman GMS90703BXA Heater
May 31, 2009 | Ruud UBHC Air Conditioner
Nov 25, 2007 | Goodman CLQ36AR49 Air Conditioner
Jan 05, 2016 | Goodman Manufacturing Goodman MSG18HRN1...
106 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: