Question about Water Heaters
Hot water continiously coming out of over flow pipe
Assuming you are talking about the temperatur/pressure relief valve, it is stuck open.
1. Turn off gas or electric to water heater
2. Close water supply to water heater
3. open hot water faucet on nearest fixture to depressurize hot water system.
4. close tpr valve (you may have to push in on the center spine. It may be resistant to closing from sediment. If so, opening and closing several times may solve that issue.
Once you get the tpr valve closed, close the faucet and open the supply valve. If the tpr stays closed, go ahead and turn on the gas/electric and re-light pilot and turn on control etc.
If the TPR blows again, you will need to replace it. YOu can buy a new one at any plumbing supply store. Shut down the heater again, drain a bit of water out using the valve on the bottom of the tank. there is probably copper pipe connected to the TPR valve which you may have to cut or maybe can just unscrew. The TPR threads out of the tank, install the new valve (make sure to use pipe dope or teflon tape.
Posted on Jan 04, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 15, 2013 | A.O. Smith Ao Smith Bt-80 Conservationist...
Mar 23, 2013 | Water Heaters
Jan 10, 2013 | Bradford White everhot outdoor tankless...
Jul 14, 2011 | Rheem 81VP6S/430126 Water Heater
May 23, 2010 | Rheem 40 Gallon FVR NATGAS Low WATER...
Mar 17, 2010 | Water Heaters
Oct 15, 2009 | Water Heaters
Jan 01, 2009 | Water Heaters
Dec 13, 2008 | Water Heaters
718 people viewed this question
Usually answered in minutes!