Question about Delfield DEL-SSR3S Spec Line 3 door refrigerator
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
I would expect at the very least a heater circuit around the freezer door. Some of the commercial units also have sprung doors to keep the doors firmly shut which you could check by opening the doors. Door heater circuits are normally very reliable and it would be worth checking the voltage is getting to them, they are also a pain to change out. Hope this helps.
Posted on Aug 26, 2007
I had a similar situation, unit cooling at about 45 deg, pressures were 10 low, 250 high.
Replaced capillary tubing, now unit cools at or below 38 deg, pressures 30 low, 225 high
Posted on Jul 24, 2009
I think it needs replacing. In some cases, the thermometer is actually the front of the controller of the unit. This could be why it runs constantly. I would also look at the condenser coils and make sure they are really clean.
let's start there. let me know if I can help further.
Posted on Jun 07, 2010
SOURCE: Does not hold temperature
start with the basics. Make sure the door closes and seals on all sides. If so, check to see that the condenser coil is clean. On some units, you may have to 'Wash" them out and let dry prior to using. Start here and let me know if I can be of further help.
Posted on Oct 16, 2010
Tips for a great answer:
Mar 04, 2015 | Delfield Refrigerators
Feb 07, 2011 | Delfield 64'' Refrigerated Sandwich Table...
Jul 26, 2010 | Delfield STD4427N Stainless Steel...
Feb 16, 2010 | Delfield Freezer Series 6000XL Remote Half...
Dec 16, 2009 | Delfield 4448N-12
Jul 09, 2009 | Delfield ST4048
Jun 14, 2009 | Delfield DEL-SSR3S Spec Line 3 door...
Aug 07, 2007 | Delfield 032-F2FH ColdPro Solid Door Reach...
19 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: