Question about Goodman Heating & Cooling
Posted by Anonymous on
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Hi I have a Goodman Furnace GMP 100-5 with an AC connected to it. How should the wireing be connected to the furnace. It does not work when we turn on the heat. Currently the furnace has a brown wire coming out with 5 wires which is connected to the brown wire from the AC unit. The furnace also has a yellow, white, brown, and green wire hanging out. The thermostate brown wire has 5 wires and the yellow wire is connected to the red wire on the AC wiring and the red wire is connected to the brown furnace red, the green wire is connected to the green wire coming out of the furnace. The other 2 wires white and blue are not connected to anthing.What is the proper way this should be wired?
Posted on Jan 06, 2010
Tips for a great answer:
Oct 10, 2016 | Goodman Heating & Cooling
Aug 26, 2013 | Heating & Cooling
Nov 01, 2017 | Heating & Cooling
Nov 08, 2010 | Goodman GMS90703BXA Heater
Apr 19, 2010 | Goodman Heating & Cooling
Oct 18, 2009 | Goodman GMS90703BXA Heater
Apr 04, 2009 | Goodman GMS90703BXA Heater
Feb 14, 2009 | Goodman GMS90703BXA Heater
Jan 07, 2008 | Goodman GMS90703BXA Heater
232 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: