Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: We have a coleman evcon
It sounds as if your furnace is exceeding the limit tempperature of the manual reset switch. The coleman is designed for the fan to continually run when this limit switch is tripped in order to keep the heat exchanger cool.( it is a safety feature) afew things may be happening.
1. the manual limit switch( the one you have to push) may be defective.
2. The fan may be running at too low of a speed. Turn power off at circuit breaker. locate circuit board on the board there will be one terminal that says heat if the red wire from the blower is on it tthen you may need to up the speed. follow the wires from the blower to the board if it has multiple speeds then you can isolate the red and put the blue or orange on the heat terminal.
3. the board may have an adjustable fan on and fan off pin selector if it is set up to come on to long or go off to soon it may not be controlling the temp of the heat exchanger properly.
4. I would also suggest checking to see if the orifices and gas valve are set up for your sytem correctly.
these are just simple ideas let me know how things go.
Posted on Oct 15, 2008
It is normal. Your house has to go down a couple more degrees because the heat pump is not working. You can solve this by rewirng you thermostat. Take off the wire that goes to Y and tape off. Then take the wires that are marked w and e or w1 and put the wires to yellow. Do not run ac with it wired like this. If you need more information please post me back
Posted on Nov 29, 2008
Sounds like they wired it direct to line voltage , it should run through a sequencer or fan relay to cycle on and off , your seq./relay could be stuck closed to but unlikely being it was just repaired , call the service company back before you do anything they are responsible.
Posted on Apr 11, 2009
My first thought is a bad thermostat or control board or maybe something is wired wrong. If all that seems to be working I would look at the outside unit. if that condenser fan motor is not operating then you wont get any cooling. look for a swollen capacitor. Read more
Posted on Jun 06, 2009
Tips for a great answer:
Nov 18, 2013 | Goodman Heating & Cooling
Jan 01, 2013 | Coleman Home Electric Furnace Eb15b/Eb15d
Nov 04, 2012 | Heating & Cooling
Jun 17, 2012 | Heating & Cooling
Mar 20, 2011 | Heating & Cooling
Dec 07, 2010 | Heating & Cooling
Feb 22, 2010 | Heating & Cooling
Feb 20, 2010 | Dometic Rooftop RV Air Conditioner
Jan 11, 2010 | Ruud UBHC Air Conditioner
Sep 01, 2008 | Carrier Heating & Cooling
25 people viewed this question
Usually answered in minutes!