Question about Fujitsu 36CS Air Conditioner
The indoor unit shows an error code with a constant flashing red operation led and the green timer led flashes 13 times.
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: System will not start up.
This is a signal fault between the indoor and outdoor first make sure the dip switches are set start with the unit closest to the condensor set as unit 1 then next unit as 2 and so on the dip switches are inside the indoor unit on the pc board if you check the manual it will tell you which swithes to set, if this wasnt done when the units where installed they would have never worked i would also check the signal wiring between the wallmount and the splitter box / bc box and make sure there isnt a loose connection when you have ruled this out id say more than likely it is a faulty indoor board on the wallmounted unt
Posted on Apr 08, 2009
Hi, that sign you get means the outdoor unit fan drive system is abnormal, and you need to call authorized service technician to check it.
Posted on Feb 10, 2011
Here error codes:ERROR CONTENTS
Here a complete service manual.
Here user manual.
Before doing anything else, power down the main circuit breaker, so to power down each unit and reset the electronics in the whole system. If all units have gone down at the same time, this will often solve the problem.
Posted on Feb 15, 2011
Tips for a great answer:
Nov 21, 2015 | Heating & Cooling
Jul 11, 2015 | Heating & Cooling
Jul 10, 2015 | Fujitsu ASU9RLS2 Single Zone Wall Ductless...
Jan 05, 2015 | Inverter Heating & Cooling
Jun 18, 2014 | Samsung AQV36JA Classic 36000 BTU Single...
May 26, 2014 | LG LMN127HVT LMN127HVT 12 000 BTU Ductless...
Oct 12, 2013 | Sharp Heating & Cooling
May 11, 2013 | Sharp Heating & Cooling
May 27, 2012 | Sharp Heating & Cooling
May 11, 2010 | Heating & Cooling
345 people viewed this question
Usually answered in minutes!