Question about Kohler 17 kW Emergency Power System - 17RES-L
Posted by Anonymous on
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
I am getting the same exact problem and errors with my 12RES Kohler generator. It will try to start using a remote switch but fails. Then it will start using the switch at the generator. The error code it comes up with using the remote start switch is usually OF or UU. It is less than a year old. Can Kohler Help??? Dave R.
Posted on Feb 20, 2010
SOURCE: UU undervoltage kohler 20kva
call koler but ui think is meant high heat as in the thermal circut is shuting you down or low oil
could be a couple of things best bet call kohler
Posted on Aug 06, 2009
On your Automatic Transfer Switch ( the little gray box you see on the right in the picture above) you have two blue buttons. One is a Manual test switch. The other has a clock on it and this is your exercise set button. Hold it down for a FULL 3 seconds if you want it to excercise without a load (not powering your home) Hold it down for a FULL 6 seconds if you want it to exercise with a load every week. Your generator will start and run for 20 minutes, and then shut down. Now every week your generator will exercise at the time and day that you pushed the set button.
Posted on Sep 04, 2009
SOURCE: my 3.5 kw kohler marine
Check that when you run it, it is not in fact making correct voltage (within about 10% is good), also make sure the engine is coming up to full speed, 3600 or 1800. You could check this with a multimeter that measure hertz. On the main output leads when the genset is running make sure it is getting close to 60 hz. or if you are in an area that uses 50 hz. check for that respectively. There are a couple things that would affect this, one would be your SCR module. There is a test procedure for this which you could find here. http://www.scribd.com/doc/50171916/tp6196-1 . I don't work on marine units, mostly standby so these manuals are for residential. Check your fuses, could even go as far as checking the wiring in the back and wiring and condition of the brushes and sliprings. These actually build field voltage to make 240 or 120 volts whatever your unit is configured to make. The brushes need to sit flat on the slip rings and on a unit with 10 hrs. the sliprings I can't imagine would be very dirty but check that as well. If you have an ADC2100 controller use this manual to go into the controller to verify that it is set for the correct voltage that the machine is built to make. The only other fairly simple thing to check that I've had issues with is if Kohler mounted a fuse block on the side of the cabinet mounted to the genset with no vibration isolation. Check these fuses while attempting to run the unit and make sure you getting steady voltage out of them as sometimes they will vibrate causing pulsed voltage to come out of them and can give you an intermittent UU, UF, or OC fault (undervoltage, underfrequency, overcrank).
Posted on Jul 16, 2011
SOURCE: My Kohler Model 17RES threw
The chattering sound is the stepper motor trying to cycle. Check to make sure there is no interference, move the throttle linkage by hand back and forth fully as sometimes the 17, 18, and 20 butterfly valve sticks on the carburetor gasket. If this happens, remove the gasket and use a file to put a good bevel (45 degree angle) in it to stop it from hitting. Thats all it takes.
Posted on Sep 06, 2011
Tips for a great answer:
May 22, 2014 | Kohler 17 kW Emergency Power System -...
Jul 11, 2012 | Kohler Electrical Supplies
Aug 09, 2011 | Kohler 12 kW Emergency Power System -...
Jul 23, 2011 | Kohler 12 kW Emergency Power System -...
Dec 10, 2017 | Kohler 17 kW Emergency Power System -...
Jul 11, 2010 | Kohler 12 kW Emergency Power System -...
Feb 04, 2010 | Kohler 12 kW Emergency Power System -...
Jan 17, 2009 | Kohler 12 kW Emergency Power System -...
131 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: