Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
3 amp is standard.the fuse is blowing to protect the transformer.It is telling you that there is a short in the low voltage wiring.Goodman also had an issue with the coil shorting on the contactor.To prevent damage.....i'd call a pro.It should be a fairly simple repair.
Posted on Jul 04, 2008
you probably purchased a 4 wire thermostat which we call heat/cool you stated you have 6 wires which signifies a heat pump you have to purcahase a heat pump thermostat and then write down the color of the wires to there related spots example...yellowe-y red-r white- w and so forth also before you do this kill the power the voltage typical for residential is only 24v's but if the wires touch you could blow a fuse
Posted on Dec 15, 2008
Wire nut or tape the black off. The red is normally 24volt supply power to the t-stat. Blue may or may not be the common. Have a voltmeter?
Posted on Jun 24, 2009
You may and an anolog stat and the old one was digital if so it won't work. Digital sends info to system anolog is just a set of points open or closed. Digital can carry tons of info to system like a computer. Like comparing a computer to a rock. Sorry but you need to go back to proper type stat.
Posted on Jun 30, 2009
Look at the contactor on the condensing unit, remove the low voltage wires to the contactor and turn on the system. If the low voltage fuse doesn't blow, replace the contactor.
Posted on Jul 07, 2009
Tips for a great answer:
Jul 21, 2017 | Goodman Heating & Cooling
Jan 09, 2011 | Shaw Robert RS-9420 Thermostat
Dec 30, 2010 | Shaw Robert RS-9420 Thermostat
Dec 26, 2010 | Heating & Cooling
Mar 06, 2010 | Shaw Robert RS-9420 Thermostat
Feb 24, 2010 | Shaw Robert RS-9420 Thermostat
Jan 08, 2010 | Shaw Robert RS-9420 Thermostat
Jun 30, 2009 | Shaw Robert RS-9420 Thermostat
Jan 04, 2009 | Hunter Fan Company 5/1/1 Programmable...
Nov 18, 2007 | Honeywell Focus 6300B 5-2 Days...
103 people viewed this question
Usually answered in minutes!