Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: 36e93 bryant furnace inop
CHECK THE PRIMARY CONTROL TO SEE IF IT IS LOCKED OUT. IF THE RED BUTTON HAS POPPED UP THEN PRESS IT ONCE TO START, IF IT DOESN'T RUN THEN CALL A TECHNICIAN. ALSO CHECK THE SIDE OF THE MOTOR TO SEE IF IT HAS GONE ON THERMAL OVERLOAD(LITTLE RED BUTTON). RESET IT AND THEN PRESS PRIMARY CONTROL BUTTON. IF MOTOR BUTTON HAS POPPED OUT THEN REPLACE MOTOR. COULD ALSO BE A BREAKER. GOOD LUCK THANKS FOR AN HONEST RATING AND FOR USING FIX-YA.
Posted on May 10, 2009
SOURCE: blower wont run
make sure getting 220 v ac on imputs the relay my be bad hook up fan man to power check to see if getting a call from stat to make fan run green to common 24v ac hope this helps
Posted on Jun 17, 2009
Hello, sincebthe motor will not run in heating and cooling the first thing to do is check the capacitor, set your meter to ohms and disscharge the capacitor with a screwdriver, if the capacitor is good the meters numbers should ramp up and down, if not the capacitor is bad. To check the motor turn off power to the unit and take you meter and measure from the common wire to each other wire coming from the motor, you should have resistance,if not the motor is bad and must be repalaced. To check the board place one meter lead on the cool/high speed motor tap and the other lead to ground, if therebis no power on a call for cooling the board is bad.
Posted on Jul 11, 2011
Hello, replace the capacitor as when there are storms sometimes they can cause a voltage spike and damage the capacitor. The capcitor will be a round or oval metal looking can next to the motor. When the blower motor runs slow the coil can start to freeze due to lack of airflow and this is why little air is coming out of the vents. If the capacitor does solve the problem then the motor will have to be replaced.
Posted on Jul 02, 2012
Tips for a great answer:
Jan 02, 2015 | Heating & Cooling
Sep 15, 2014 | GE Carrier Bryant Furnace 1/2 Hp Ecm...
Jul 13, 2014 | Bryant Heating & Cooling
May 27, 2014 | Bryant Heating & Cooling
Oct 08, 2013 | GE Carrier Bryant Payne 2.4 Hp...
Nov 26, 2012 | Bryant Heating & Cooling
Jul 01, 2012 | Bryant Heating & Cooling
Nov 09, 2008 | Bryant 462AJC021BA Air Conditioner
39 people viewed this question
Usually answered in minutes!