Question about Heating & Cooling
Outside unit is not working seams that not power there.
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: lg split system air conditioner
Try sutting off the power to both units. This may reset the unit. Check out the service manual at LG website www.lgusa.com. Go to their support page and put the model number in. Remove and replace the batteries in the remote. If there is a communication error, the inside unit will display 3 flashes. If all else fails, call LG at 1-800-243-0000. Good Luck!
Posted on Aug 30, 2007
SOURCE: air conditioner
Remote control units have diagnostic program in the
control, after 3 to 5 minutes of operating if the diagnostic
tools detect abnormal operation, then its shutdown the unit
to protect from damage. Thermistor sensor is one of the
parts that detect the operation of the unit. Out of range
or defective thermistor can shut the operation of the unit.
- If your indoor and outdoor is clean start the unit in cool mode and monitor the outdoor pipes. If your suction pipe is icing or dry then your unit is under charge, but if your suction is cold and sweating then the system is ok and sure that the thermistor sensor is defective.
- Out of range thermistor sensor in both return air and freeze up sensor can cause the tripping “off “ the unit. The resistance of both thermistor is 8 to 10k ohms, so can test by using ohm meter
Posted on Jan 12, 2008
It sounds like your condenser fan motor may be locked up or the capacitor that helps give the condenser fan motor a kick to get it started may be defective. Try turning your system on and using a long screwdriver try to push the fan blade on the condenser fan motor to see if it will run normally if you give it the starting boost it needs.If it does run at full speed and doesn't over heat or start and then slow down then you probably only need to replace a simple 10-12$ capacitor. If it barely turns, makes an odd humming sound or overheats etc. then you will have to replace the condenser fan motor. This is assuming that the outdoor condenser has the 220v supplied and the 24v supplied to the compressor relay, that the compressor relay is engaged and suppling 220v to the condenser fan motor.
Posted on May 30, 2008
Tips for a great answer:
Jul 18, 2010 | Carrier Heating & Cooling
Sep 27, 2009 | Goodman CLQ36AR49 Air Conditioner
Jun 10, 2009 | Carrier 38CKC036 Air Conditioner
Jan 09, 2009 | Friedrich QuietMaster Electronic SS12J30D...
Aug 22, 2008 | Goodman CKL30AR30 Air Conditioner
Aug 19, 2008 | Whirlwind FH-778 Air Conditioner
Jun 24, 2008 | Ruud UAKA030 Air Conditioner
Jun 15, 2008 | Samsung AS18A6RB Air Conditioner
May 06, 2008 | Weather King 10AJA2501AH Air Conditioner
Nov 21, 2017 | Heating & Cooling
51 people viewed this question
Usually answered in minutes!