Question about Electrical Supplies
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
A call to Elliott Small Engine solved my problem - Oil Guard. I had checked the oil and it was just a little low but seemed well within the normal range. I was told to add more, bringing it just over the Full mark. It seems that the low oil protection system is very sensitive and shuts down the engine even when the oil is withing 1/8" of the mark. I added about 2-3 oz of oil and no more problems
Posted on Dec 16, 2008
SOURCE: Generac Guardian 15kW Generator
That sounds just about right, if the relay contacts get welded together it sometimes takes out the driver on the printed circuit board. As you found out, 12vdc from 23 to 194 makes the transfer switch move to the Generator position, relay not energized makes the ATS move to the Normal position.
You can make a nice test function by installing a 10 amp contact switch in series with either the N1 or N2 terminals. When the switch is open the generator thinks the Normal power has failed.
Posted on Jan 26, 2009
First drain the fuel bowl. Any old fuel in there will keep it from starting. Fuel stabilizer is not what it's it cracked up to be. I've worked for 6yrs at a rental yard and had no luck with any fuel stabilizer, the fuel still went bad. If after you drain the fuel bowl it still will not start, you will need to clean the carb. Remove the carb and spray carb cleaner through all the accessible passages. If this does not do it, you will need to replace the carb. For long term storage I highly recommend draining all the fuel and filling just the carb with fuel stabilizer to keep gaskets moist. Then drain the carb when you take it out of storage.
Posted on Mar 30, 2009
I am assuming the generator worked fine before the oil change. Now that you have done the oil change the genset does not start. These generators have a safety switch, which is basically an oil pressure switch that keeps the engine from running when there is not enough oil in the engine. Make sure that there is enough oil and if there is, look for a wire that runs along side of the engine to a round component. disconnect that wire and try starting. If it does not start then try to ground out the wire to the engine block. If this does not work, then there is other engine problems.
Posted on May 08, 2009
Tips for a great answer:
Sep 30, 2012 | Generac 6500 Watt Gasoline Generator - 49...
Nov 05, 2011 | Generac Guardian Ultra Source 15,000 Watt...
Aug 22, 2011 | Generac Guardian Ultra Source 15,000 Watt...
No Battery Charge DC output.
1. Battery posts are corroded. 1. Clean battery posts.
2. Battery cable is bad. 2. Replace cable.
3. Battery is defective. 3. Check battery condition; replace if
4. Receptacle is bad. 4. Contact Authorized Service Facility.
Hope this helps!
Jun 02, 2011 | Generac Guardian Ultra Source 15,000 Watt...
Apr 27, 2011 | Generac Guardian Ultra Source 15,000 Watt...
Jan 20, 2010 | Generac 13,000 Watt / 13,000 Watt Home...
Jun 20, 2009 | Generac Guardian Ultra Source 15,000 Watt...
Apr 05, 2009 | Generac Guardian Ultra Source 15,000 Watt...
Aug 16, 2017 | Mr Steam Electrical Supplies
83 people viewed this question
Usually answered in minutes!