Question about Briggs Electrical Supplies
Doesn't seem to be getting any spark.
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Briggs & Stratton Burnt Brushes
I did find out that the inner slip ring was worn down. Still unknown why and the repair tech we took it to twice just replaced the brushes and never looked at the slip rings.
My solution, which has worked for over two months now (knock on wood) is as follows:
The slip ring on this unit can only be replaced by replacing the whole rotor assembly. I looked at the width of the brushes and the width of slip rings. The slip rings are twice as big as a brush. The solution was to move the brushes outward by one brush length. In order to do that, I had to turn the brush assembly around because of the extra plastic on the unit and space it out one brush length. Note: Still hook the wires as if the brush assembly was not turned around.
I used an old brush assembly and cut the two areas where the screws go through to make my spacers and it works perfectly.
Posted on Dec 03, 2008
SOURCE: stops and starts
Most home standby generators are setup to run once a week so as to keep the engine lubed up and the generator windings dry. So if yours is comming on once a week at about the same time and running for something like 15 minutes, that's what is going on.
On the other hand, if your generator is starting and the switch is transferring somewhat randomly, you could have a problem with the neutral connection in your system, the power could really be going out and coming back on, and/or the control board in your generator could be broken.
Posted on Mar 15, 2009
I am assuming the generator worked fine before the oil change. Now that you have done the oil change the genset does not start. These generators have a safety switch, which is basically an oil pressure switch that keeps the engine from running when there is not enough oil in the engine. Make sure that there is enough oil and if there is, look for a wire that runs along side of the engine to a round component. disconnect that wire and try starting. If it does not start then try to ground out the wire to the engine block. If this does not work, then there is other engine problems.
Posted on May 08, 2009
The needle valve may be stuck which would not let gas into the carb. I don;t think rebuild kits are too expensive. Pull the carb and take it to a lawnmower repair shop and they should have the parts. Before that though pull the bowl and make sure it has gas in it. If no then remove the fuel line and make sure gas flows from it. If no then could be the fuel shutoff valve is not operating properly or junk in the gas tank is obstructing the line.
Posted on Jul 31, 2009
Tips for a great answer:
Aug 27, 2012 | Briggs & Stratton Electrical Supplies
Jul 24, 2012 | Briggs & Stratton Briggs Stratton Intek V...
Jul 01, 2012 | Troy-Bilt Chipper Shredder
Apr 23, 2012 | Briggs & Stratton Garden
Mar 05, 2017 | Briggs & Stratton Measuring Tools &...
Nov 01, 2011 | Coleman Powermate Powermate 5000W...
Jul 09, 2011 | Briggs & Stratton Briggs Stratton 7 kW...
May 01, 2011 | Briggs & Stratton Briggs and Stratton...
Jan 16, 2009 | Briggs Stratton H7159 & Stratton® 5500,...
44 people viewed this question
Usually answered in minutes!