Question about Fujitsu Heating & Cooling
System has been vacuumed, trying to charge system needs 1.9kgs of R22 outside temp: 14oc, have connected refrigerant hose to system and 30grams has gone in. Have applied heat above indoor unit to make indoor unit think it needs to ask for cooling. This has not worked has any one got any suggestion. Have not had much experience with R22.
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Will Not Heat
On the outdoor unit the fan should not be running, on the indoor unit the fan should be running. If you then check the outdoor unit with fan not running, you should be able to hear clearly that the compressor is actually working. If this is all correct, it is possible that your fourway reverse valve is seeping and needs to be replaced.
Posted on Apr 15, 2009
If anything, it appears undercharged. Purging is not recommended. @90 degrees the high side corresponding pressure is 168.4 and Low side coresponding numbers re70psi/68degrees. With all due respect to the tech I think . If your room temp is 80, the corresponding high aide pressure is 143.6 , Low side 85 psi Yup, undercharged. Now do me a favor and don't start any "but he said" wars going. If anything, Just call him back and tell him something is still not right. Ask him to bring you a pocket rergerence for temp/pressure relationships. The numbers I gave you are for R-22 which is commonly used in residential applications. Well, good luck and keep your cool. IDon't purge. R-22 is very expensive asis everything else. You may want to dispute anny additional service call charges. Good Luck
Posted on Aug 22, 2009
The front cover can be dismantled (taken off as one Piece) by unscrewing the screws at the bottom of the air outlet (they are covered by screw cvers which will need to be taken off. Then just pull off the cover. PLEASE NOTE that the front panel (liftable to take out filters) will need to be removed lift up until 90 degrees and then pull off gentley and also take out filters before removing front cover
I take the time to answer you questions so please rate me
Posted on Aug 29, 2009
First check your circuit breaker or fuse that supplies power to the outside unit. It's probably separate from the inside unit. Then try to turn unit on. If the fan and compressor just make a humming sound then turn it off and check the capacitor if you have a multimeter. You can also look at it and see if the top looks expanded. That's a good sign its bad, but not all bad one's look expanded. Tomorrow I will have access to an LG service manual and can let you know what the code means. Sorry I can't get it sooner. Let me know what you find.
Posted on May 03, 2010
Tips for a great answer:
on Dec 16, 2010 | Refrigerators
Jun 09, 2011 | Heating & Cooling
Jan 02, 2011 | Daewoo Heating & Cooling
Aug 15, 2010 | Whirlwind FH-778 Air Conditioner
May 26, 2010 | Heating & Cooling
Feb 21, 2010 | GE Quiet-Aire Ductless Heat Pump Split...
Nov 10, 2009 | Fujitsu 24C1 Air Conditioner
Feb 23, 2009 | Cfm Daikin R410a Split System Air...
Nov 16, 2008 | Computers & Internet
17 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: