Question about Water Heaters
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
the problem is the diverter valve unit, source a corgi engineer to fit new one, cost for valve approx 80 quid +fitting
Posted on Dec 16, 2008
got your fix, its a calcium buildup in the heat exchanger, and more than likely the rest of the unit, you will need to flush the unit with about 4 gallons of vinegar, you will need to recirculate it for about 20 mins through the unit, then flush with clean water, hook it back up, it might take a couple of mins for it to run properly, but it will, I have had the same problem with Rinnai on demand hot water systems, and it worked like a charm, check the filter thats inline as well, make sure it isnt plugged, clean if needed, also if you dont have a soft water system inplace, you might want to think about buying one and having it installed, that will reduce this from happening again for alot longer period of time, hope that helps
Posted on Jan 20, 2009
refere to manual check for override switch loss of pressure no problem re-pressurise and check for leak top of rad valve good place to start
Posted on Oct 11, 2009
Tips for a great answer:
Apr 14, 2016 | Water Water Heaters
Mar 13, 2016 | Water Water Heaters
Sep 23, 2014 | Water Heaters
Mar 01, 2014 | Water Heaters
Mar 02, 2017 | Water Heaters
Jul 16, 2009 | Water Heaters
Jan 20, 2009 | Water Heaters
Dec 15, 2008 | Water Heaters
55 people viewed this question
Usually answered in minutes!