Question about Hardware & Accessories
Check circuit breaker.
Click fully off and then back on.
Check for burned smell at breaker or loose crackling sound that says breaker is bad.
Reset timer. Then Reprogram.
Possible geyser timer manual
http://waterheatertimer.org/pdf/Digital-Geyser-Timer 24H-7-Day-Timer-230V Brochure.pdf
This timer has a non-replaceable internal rechargeable battery.
If battery has gone bad, then timer is defunct.
Use manual override button to turn timer ON-OFF.
Then test across terminals 3 and 4 for 240Volts.
Turn timer OFF, and test across terminals 4 and 5 for 240Volts
If no voltage shows then timer does not have output.
If test shows 80% undervoltage, that can cause load not to activate, depending on type of load.
Have electrician check for voltage issues at power company transformer.
Unknown what load timer is connected to.
Max load for this timer at 240 volts is 3680 watts, 16 amps.
Motor load is 230 volt 8 amps.
Check label on load for watt or amp rating.
Volts x amps = watts
Watts divided by volts = amps
Posted on Nov 01, 2012
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 11, 2015 | Grundfos Hardware & Accessories
Sep 19, 2014 | Hardware & Accessories
Dec 11, 2013 | Vehicle Parts & Accessories
Oct 31, 2013 | Hardware & Accessories
Feb 07, 2012 | Hardware & Accessories
348 people viewed this question
Usually answered in minutes!