Question about Heating & Cooling
I had a brand new boiler installed by a recommended supplier in September 2008. It failed to heat the hot water . After some time and aggravation we were advised a new pump was required. This was fitted in November. By December it was not working again and we were getting no hot water from the boiler and by January 5th the central heating system was not working either. The lights are on, on the control panel.
It sounds like the system was not cleaned properly when the new boiler was fitted. all new boilers need to have the pipework flushed to remove any debris scale sludge and flux from the system. this is now usually done by a power flush which is basically a big pump mounted on a big bucket and it washes the dirt out of the pipework and collects in the bucket. if this is not done the dirt will block up the small passages in the heat exchanger. i suggest the system is cleaned flush and the heat exchanger changed to help protect the boiler a filter should be fitted (for example a magna clean) if the company who installed the boiler is corgi registered then they are liable for the damages. call corgi for advice.
Posted on Mar 26, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 08, 2017 | Miscellaneous
on Dec 06, 2009 | Heating & Cooling
Feb 06, 2015 | Water Water Heaters
Aug 19, 2014 | Heating & Cooling
Mar 22, 2017 | Water Heaters
Mar 27, 2010 | Heating & Cooling
Jul 10, 2009 | Whirlpool Aquatic Millennium VII -...
May 03, 2009 | Bosch & Power Vent Water Heater
Dec 18, 2008 | Protech Systems FasNSeal FSWMKE4 4" Vent...
Dec 15, 2008 | Home
588 people viewed this question
Usually answered in minutes!