Question about General Electric 100Amp 3-pole circuit breaker
You should repair your zinsco panel... go to my website at zinscoelectrical.info , and get a new buss bar and breakers.... Good luck
Posted on Aug 12, 2011
The screw is loose. It is always HOT (has electricity going to it) so be careful. If you feel confident, cover a screwdriver with a few layers of electrical tape and tighten it. Depending on how long it has been arcing, the breaker will need to be replaced. Since the incoming wire will have power to it, have a licensed electrician do the job. He will possibly remove the meter head to cut the power while he does the work.
Posted on Jan 03, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 26, 2014 | Electrical Supplies
Nov 17, 2013 | Cutler Hammer "WESTINGHOUSE" MAIN DOUBLE...
Feb 21, 2013 | Bryant /murray Bj2200 Main Circuit Breaker...
May 23, 2011 | Connecticut Electric UBIZ0215 Zinsco...
Oct 17, 2010 | Challenger 30 Amp 2 Pole A230 A Circuit...
Mar 08, 2010 | Your One Source Homeline Load Center, 200...
Jan 26, 2010 | Eaton 20A ARC FAULT BREAKER
Jan 18, 2010 | Cutler Hammer "WESTINGHOUSE" MAIN DOUBLE...
Dec 17, 2008 | Prime 10 Amp Circuit Breaker
Dec 15, 2008 | Fahrenheat LFP6152 Halogen Baseboard...
188 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: