Question about Heating & Cooling
I just installed a new-old-stock (2006 R22 scroll compr.) Amana condensing unit and matching Goodman air handler in an older house with existing vapor and liquid lines. I am a certified tech (10 years ago) with no experience. Now that I have the system installed I need to evacuate the lines and air handler I understand the condensing unit is pre-charged. I've discovered that the service ports on the condensing are not open to the lines so I can't evacuate unless I release the pre-charged R22 into the contaminated lines and air handler. Do I have to cut the lines and install a service port to evacuate the system?
I've never seen service ports that are not connected to the lines. They should be. If you gently push on the shraeder core there should be no pressure. Once you open the valves, then you have pressure. So you must pull a vacuum on the lines, as you already know. How did you learn that the ports are not connected to the lines? They have pressure? Not sure what's going on but something's different.
Posted on Apr 12, 2017
The service valves are closed. Therfore once you solder to the stubs on the valves your gauges will read what is in the line set and evaporator coil. Pressure test to 150 and let sit. If determined your pressures held then evacuate with vacuum pump. You are evacuating the line set and evap coil only because your service valves are closed. THIS IS THE PROPER WAY TO DO THIS. Once evacuated to 500 microns, close manifold and open valves. You will then see your refrigerant charge and determine if more refrigerant is needed. Good Luck !!
Posted on Apr 11, 2017
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
I've done what you are describing - "however" you could void the warranty on the new condenser - by not having 'matching' coils (inside/outside). I would do some serious checking with whoever you are buying the new condenser from.
Note: I would (if possible) go back with a R-22 condenser unit (price is about the same), and you would not have any 'warranty or matching issues' going on.
Posted on Jun 07, 2011
Tips for a great answer:
Feb 14, 2015 | Amana Goodman R-410A Heat Pump Condenser 2...
Apr 20, 2014 | Goodman CLQ36AR49 Air Conditioner
Apr 20, 2014 | Goodman CKL42AR42 Air Conditioner
Jun 03, 2011 | Heating & Cooling
Here is a tip about Mitsubishi Air Conditioners and how to get the manuals for all of the Mitsubishi line. The manual include both troubleshooting and installation.
Mitsubishi Air Conditioner Troubleshooting and Repair
Oct 06, 2010 | Mitsubishi Heating & Cooling
Sep 08, 2010 | Goodman CKL42AR42 Air Conditioner
Jun 26, 2010 | Goodman CLQ36AR49 Air Conditioner
May 19, 2010 | Carrier 38CKC036 Air Conditioner
Nov 15, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jul 12, 2009 | Coleman Heating & Cooling
Feb 22, 2018 | Mr. Heater Heating & Cooling
52 people viewed this question
Usually answered in minutes!