Question about Heating & Cooling
I am unable to locate the location of the air filter for Aqua Therm indoor furnace model 24UAQ3
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: model ckl 60-1 furnace is
Check the thermostat and see that it is set to the cooling mode. Outside unit may not be powered up, check breakers for A/C and insure that it is turned on.
Posted on Apr 29, 2008
SOURCE: no air blowing through ducts
If the inside fan motor is still running but you have no air flow it could be low refrigerant charge, dirty evaporator coil, or just leaving the temperature set point to low over night when it was cooler outside, causing the evaporator to freeze up stopping the air flow. Once the evaporator coil has started to collect ice it must be completely defrosted before the problem can be corrected.
Example, It could be that your coil froze due to a dirty filter, which you have now replaced, but the evaporator coil has not had a chance to completely defrost.
I would turn off the A/C but set the fan to on for at least four hours, if you can see the drain from the unit wait until not even a drop of water is coming from it. Then turn the A/C back on and check it, it is important to leave the A/C off the full defrost time, if it is turned on even for a few minutes at a time it will never defrost.
After you restart the A/C if it cools ok for a while then does the same thing again it is probably low refrigerant charge and you should have a service company check it.
Posted on May 22, 2009
look for a cover that covers the a A coil.take the small 1/4 in screws out and carefully remove the covers or cover if you have access do both sides. my basement has enough room to get to both sides. my house tlr you can only do one side. look for a drain hole blow it out with a air hose or garden hose run a wire if you have to.
Posted on Aug 01, 2009
verymuch so it is clogged up , now open system treat drain pan with bleach ,blow out two lines if there are available but if theres only one treat that on ,then treat the coils clean an treat them after cleaning pour little bleach in the bottom of the pan
Posted on May 24, 2010
Tips for a great answer:
Mar 19, 2016 | Filter Heating & Cooling
Jul 02, 2015 | Filter Heating & Cooling
Sep 13, 2014 | Heating & Cooling
May 31, 2011 | GE Zoneline AZ58H12DAD Air Conditioner
Jun 25, 2010 | Carrier 38CKC036 Air Conditioner
Jun 18, 2010 | Heating & Cooling
Apr 05, 2010 | Heating & Cooling
Feb 02, 2010 | Goodman Heating & Cooling
May 27, 2009 | Carrier Heating & Cooling
64 people viewed this question
Usually answered in minutes!