Question about Heating & Cooling
Can you remove the front cover to the wall unit? Look for the wiring and follow it till you see a round about the size of a fifty cent piece. Should have 3 of them. One of them is not closing and allowing the signal to go through. So turn up the t-stat to call for heat take each one of the limit switches and by pass them one by one till you find the one that is bad. Depending on where you hit the cover is where I would look first. The limit's are rated by temperature so replace with correct size. You should be able to see the temp. on the limit something like 180 is what you are looking for. Also make sure the wires are in good shape where they connect to the switches. Might have a loose connection. ken
Posted on Jan 03, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 27, 2015 | Cozy Heating & Cooling
Feb 22, 2015 | Cozy Heating & Cooling
Dec 19, 2010 | Cozy (W352E) Heater
Nov 27, 2010 | Cozy (W352E) Heater
Nov 07, 2010 | Cozy (W352E) Heater
Apr 30, 2010 | Cozy Enclosed Front Console Heater 20,000...
Mar 01, 2010 | Cozy (W352E) Heater
Jan 09, 2010 | Cozy (W352E) Heater
Jan 31, 2009 | Cozy (W352E) Heater
97 people viewed this question
Usually answered in minutes!