Question about Coleman Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
the fan motor bearings need lub....the shaft has a tiny access hole to put some oil into. because the fan shaft is slowing down, it is putting more strain on the voltage current, and eventually the internal breaker shuts down the ac........plus your condenser is not getting enough air accross it, compressor heats up, and it too will shut the unit down......older units have to be oiled every year, and eventually it too will fail, and a new blower motor assembly is needed or replace the ac unit.....blower motor units are around $130....now you install it or pay to have it done at around another $150 labor,,,,,try yourself, if it fails then call the tech........let me know ..ray..firstname.lastname@example.org
Posted on Dec 31, 2008
SOURCE: No cold air
1.The selector switch may be open.
2. Thermostat may be open.
3. Overload switch may be open.
4. Compressor winding may be open.
and rotate the switch to the proper position and read
continuity as follows:
Terminals Switch Position
L-1-3 Lo Heat
L-1 Lo Fan
L-2 Hi Fan
L-1-4 Lo Cool
L-2-4 Hi Cool
The compressor motor is located inside the hermetic
compressor housing and therefore not accessible for service or
visual observation in the field. However, the motor winding
condition can be analyzed by using an ohm meter. Be sure to
remove all the leads from the compressor terminals before
making this check.
1) If the resistance between any two terminals is 0
ohms, the motor windings are shorted.
2) If the resistance between any terminal and the
compressor housing is anything but infinity, the
winding is grounded.
3) If the resistance between any two terminals is
infinity, the winding is open.
On a good compressor, the highest resistance will be between
the R (run) and S (start) terminals. The lowest resistance will
be between the C (common) and R (run) terminals. The
intermediate resistance will be between the C (common) and
S (start) terminals. Notice that compressors have the
identification of the terminals marked on either the terminal
cover or on the compressor housing.
There are several capacitor test devices available. The ohm
meter is one of them. The ohm meter cannot verify a
capacitors MFD (microfarrad) value. However, the following
procedures will show you how to use an ohm meter to
determine if the capacitor is good, open, shorted or grounded.
Before testing any capacitor, always perform the following
* This test must be done with a analog type meter.
a) Disconnect all electrical power to the air conditioner.
b) Discharge the capacitor with a 20,000 ohm (approx.
3 watt) resistor or larger.
c) You may discharge capacitors with a standard volt
meter if you use a scale over 500 volts and touch the
leads (one lead to each side of the capacitor). The
volt meter will discharge the capacitor.
d) Identify and disconnect the wiring from the
e) Set and zero the ohm meter on the “highest” scale.
When testing for a good, open or shorted capacitor,
perform the following checks: Place the ohm meter
leads across the capacitor terminals (one lead on
each terminal) and perform a continuity test. Then
observe the action of the meter needle or indicator.
Reverse the leads and test again. The result should
be the same. Note: If the capacitor had not been
properly discharged, a false reading could be
indicated on the first test. Always test several times
(reversing the leads with each test). This will verify
the capacitors condition.
If the capacitor is good, the indicator will move from infinity
(the left side), towards zero ohms and slowly return back to
infinity. Reverse the leads and test again. The result should
be the same.
Most models use a start capacitor and a start relay to give the
compressor high starting torque. The compressor will,
therefore, start against normal pressure difference (head
pressure minus suction pressure) even when shut down for a
short period of time. The start relay will disconnect the start
capacitor when the motor reaches approximately 75%
Start (Potential) Relay
The start relay consists of –
1) Normally closed contacts internally between
terminals #1 and #2 which switch in the start
capacitor in parallel to the run capacitor during shut
down and then switch out the start capacitor when
the motor reaches approximately 75% normal
2) A high voltage coil internally between terminals #5
and #2 to actuate the contacts. The coil is too weak
on line voltage to actuate the contacts, but it is
connected in series with the start winding and it gets
the generated voltage of the start winding portion of
the compressor motor. This generated voltage is
much higher than line voltage and varies with the
speed of the motor. Therefore, since the relay is
designed to open the contacts at 75% of normal
running voltage (measured between terminals #5 and
#2), the contacts will open (thus disconnect the start
capacitor) at approximately 75% of normal running
(B) Positive Temperature Coefficient Resistor
(Commonly Known As PTCR Start
The resistor acts like a potential relay in that it takes the start
capacitor out of the start circuit, but uses resistance of
electrical flow (back EMF from compressor) instead of
opening a set of contacts. The service person should be careful
handling the resistors. They will be hot during operation (up
to 160 degrees F). The air conditioner needs to be off for 3-5
minutes during cycle time and when servicing to let the
resistor cool down.
That covers everthing.
Please rate this a fixya
Posted on Feb 09, 2009
are you speaking of the outside fan or inside? compressor should be a little warm but not boiling hot. the unit could be low on freon. if low it will run a while but the compressor will overheat and shut off leaving the fan running by itself ouside. if nothing outside is running check power. if you have power check the contacted outside to make sure it's pulled in. contacters are bad about going out on goodman untis. Also ants can get under contacts.
Posted on Jun 18, 2009
This unit is use in motels etc. Check the ouside coil ( conderser) from the inside (discharge fan ) for dirt. Most of these units are floor level . This can cause a unit to short cycle ( cold air is at the floor) .
Posted on Jul 18, 2009
Tips for a great answer:
Sep 12, 2011 | Coleman Mach III Air Conditioner
Aug 18, 2011 | Coleman Mach III Air Conditioner
Aug 30, 2009 | Coleman Mach III Air Conditioner
Aug 17, 2009 | Coleman Mach III Air Conditioner
Jul 20, 2009 | Coleman Mach III Air Conditioner
Jul 01, 2009 | Coleman Heating & Cooling
Jun 26, 2009 | Coleman Mach 15 Air Conditioner
Apr 06, 2009 | Coleman Mach III Air Conditioner
121 people viewed this question
Usually answered in minutes!