Question about Goodman Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
The Ignitor on my furnace glows and fades. I do not hear anything blowing either as I watch the ignitor get bright orange..then fades.
Any answers? I tried to look here on this site but have not seen anywhere where there is a solution. I was going to replace the entire gas valve assembly because I am guessing the problem is with the coils sicne the ignitor fades away.
Posted on Dec 16, 2007
You have a limit switch located in the furnace (a little bigger than a dime and located near the center of the front panel, sometimes the switch is mounted to a small fiberglass board) . There will be two wires going to it. They sometimes trip so often that they fail to automatically reset(due to dirty filters or undersized ductwork). You can SHUT OFF POWER TO THE FURNACE, then remove the two screws holding the switch in the furnace, pull the switch out of the furnace and tap on it and wipe it off.
The switch may work a few more times but should be replaced with the same size and type. You will see some rating printed on the switch somewhere. Write down all the numbers and get a replacemet from a furnace/AC supply house. If you have a meter and know how to use it you could check the switch for continuity.
Sometimes just a tap on the switch will get it going. There will also be a couple of rollout switches that could be tripped. They have little buttons on them to reset them. If they trip it may have other issues to be solved.
Hope this helps!
Posted on Feb 01, 2009
SOURCE: gfci breaker for spa
gfci's are designed to trip if they receive voltage on there ground/neutral side, therefore my vote is for Smithbrother I would say there is probably a partial short somewhere in you system.
Posted on Mar 24, 2009
Is the blower wheel turning? Did you by chance have to remove the motor from the blower wheel to work on it? If you did, did you put the blower wheel back on in the correct direction of air flow? Also, did you put the correct capacitor back on the unit so it can get up to the required rpm's? These are things that you will need to check for. If the motor is running and the blower wheel isn't and the wheel is tight on the shaft, then you will have to replace the motor. The brushes may be bad on the unit and it's not turning the shaft. Hope these ideas help.
Posted on Apr 10, 2009
Sounds like motor has failed. If the red light is blinking it may be telling you what is wrong by the number of blinks. It maybe locked out for some reason or loose wire. Try turning off breakers to inside unit for 5 mins and try again, this may reset unit. But it sounds like a bad motor or circut board. Try running with stat in on position instead of auto in cooling mode.
Posted on Jun 28, 2009
Tips for a great answer:
Jan 01, 2015 | Goodman Manufacturing Goodman GPH1348M41 4...
Feb 10, 2013 | Goodman Manufacturing Goodman...
Jul 12, 2011 | Goodman CKL36AR36 Air Conditioner
Jul 05, 2011 | Heating & Cooling
Jun 10, 2009 | Goodman CKL30AR30 Air Conditioner
Dec 19, 2008 | Goodman CLQ36AR49 Air Conditioner
38 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: