Question about Goodman Manufacturing DSZC160481A/GMVC951155DX/CAPF4961D6 4 Ton 16 Seer 95% Efficient 115,000 BTU Variable Speed Goodman Gas Furnace / Electric R410a Hybrid Heat System
Heater barely gets up to temperature
You might try checking your return filter. The new filters (pleated 3 month, ie real expensive ones) cut back your air flow 35% from the amount the regular 30 throw away allow. When air flow reduces the temperatur from furnace increases and can cause inadvertant high temperature limits to trip. If you are using a clean return filter, next you need to physically observe the air inlet side of your cooling coil to see if it is blocking air flow due to being dirty. If you have trouble with seeing the inlet, you might need to get a professional to take the air handler apart.
Posted on Apr 15, 2014
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get to try the service completely Free afterwhich it costs $6 per call and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 10, 2015 | Vulcan Heating & Cooling
Feb 21, 2015 | Heating & Cooling
Here is a tip that will help you try to figure out why your furnace is not working.
Basic Furnace or Heating System Troubleshooting
Feb 19, 2011 | Goodman GMS90703BXA Heater
Feb 10, 2011 | Coleman Heating & Cooling
1. Thermostat calls for heat. 2. Draft inducer motor starts. 3. Pressure switch attached by a small plastic or rubber tube senses the negative pressure produced by the draft inducer and closes. 4. Draft inducer runs for 30 seconds to a minute before you hear a gas hissing sound. The ignitor did not glow, the flame sensor (a small metal probe about 1/8" in diameter, with a white porcelain base) does not sense the flame, so after 8 to 10 seconds the hissing sounds stops with no ignition of gas to heat your home. Your furnace shuts down and goes into a lock out condition until you turn your power switch back off and on again. Then the sequence starts all over again with no ignition of the gas. Solution:You probably need to purchase and install a new ignitor. I would suggest that you inspect your ignitor closely for cracks. Make sure you do not touch the ignitor with your bare hands. If you do not visually see a crack, then you could have a furnace control board problem or a limit, rollout switch problem. The furnace's control board might not be supplying the voltage to the ignitor.If your furnace lights and the gas stays on for 8 to 10 seconds, then shuts right back off, then you need to clean your flame sensor with light sand paper or steel wool. You might need a new flame sensor, but most of the time they can be cleaned an will work well after cleaning.
Dec 11, 2010 | Mr. Heater Natural Gas Garage Heater -...
Setting a thermostat has nothing to do with outdoor temperature, but more to do with what is a comfortable setting for you and your utility bill.
A common misconception associated with thermostats is that a furnace works harder than normal to warm the space back to a comfortable temperature after the thermostat has been set back, resulting in little or no savings. This misconception has been dispelled by years of research and numerous studies. The fuel required to reheat a building to a comfortable temperature is roughly equal to the fuel saved as the building drops to the lower temperature. You save fuel between the time that the temperature stabilizes at the lower level and the next time heat is needed. So, the longer your house remains at the lower temperature, the more energy you save.
Another misconception is that the higher you raise a thermostat, the more heat the furnace will put out, or that the house will warm up faster if the thermostat is raised higher. Furnaces put out the same amount of heat no matter how high the thermostat is set; the variable is how long it must stay on to reach the set temperature.
In the winter, significant savings can be obtained by manually or automatically reducing your thermostat's temperature setting for as little as four hours per day. These savings can be attributed to a building's heat loss in the winter, which depends greatly on the difference between the inside and outside temperatures. For example, if you set the temperature back on your thermostat for an entire night, your energy savings will be substantial. By turning your thermostat back 10 to 15 degrees for 8 hours, you can save about 5 to 15 percent a year on your heating bill -- a savings of as much as 1 percent for each degree if the setback period is eight hours long.
Hope this helps..........
Nov 23, 2010 | Goodman GMS90703BXA Heater
Jan 11, 2010 | Honeywell Electronic Programmable...
Jan 02, 2010 | Goodman GMS90703BXA Heater
Dec 29, 2009 | Heating & Cooling
Dec 29, 2009 | Dayton Gas Furnace Heater
57 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: