Question about Dayton Heating & Cooling
100 thousand but moldel # 3e370b serial # q9462424
100k input is about 80k output, and this will typically be on a 1,200-2,000 sq ft home depending on ceiling height and location ,Montana or Los Amgeles?
Posted on Oct 31, 2012
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
I'm assuming your heater is the little Cozy direct vent wall furnace, your room calculations are correct, and at 57 degrees your main burner is constantly on. If so, it sounds as if you have too low a flame which can be caused by a main burner jet with an undersized orifice (like a propane one that got in the wrong assembly line) or obstructed by dirt, inadequate gas pressure, or a main gas valve that is not fully opening.
Open the pilot light inspection door and look at the main burner flame height. If it is less than 2 inches or so, check out the three possibilities above. If the flame is very yellow and wandering around lazily, check the air intake on your vent cap for obstruction.
Posted on Mar 15, 2009
I have a manual for a Dayton 3E218E. If you want a copy email me at Edwards0202@aol.com and put "HEATER MANUAL" in the subject line. I can scan it in and email it back to you. This manual is for 2E510F, 2E511F, 3E218E and 3E219E. I also found a great web site for parts for all these models as well:
Posted on Jan 18, 2010
Tips for a great answer:
Jan 05, 2016 | Dryers
Mar 10, 2015 | Blue Wave Swimming Pool & Spa Above-Ground...
Sep 22, 2011 | Whirlpool Duet 7.0 Cu. Ft. 7-Cycle Super...
Sep 12, 2011 | Mr. Heater MRHMH18B Gas Utility
Aug 12, 2011 | Fedders Heating & Cooling
Jun 13, 2011 | Fahrenheat F25426 Electric Baseboard...
Feb 01, 2011 | Dyna-Glo Double Tag-a-long Heater
Jan 05, 2018 | Dayton Gas Furnace Heater
Jan 09, 2011 | Dayton Gas Furnace Heater
Apr 16, 2018 | Dayton Heating & Cooling
76 people viewed this question
Usually answered in minutes!