Question about Heating & Cooling
I would like to know the current requirement that the thermopile needs to provide?
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
This is a weird one, but make sure all the wire connections are in the correct place. I accidentally miss wired a heater like this and it did the same thing.
Posted on Dec 18, 2007
you need to check the generator in series with flame present. remove one wire from gas valve.put 1 of your meter probes under gas valve terminal where you removed one lead from powerpyle generator.put generator on other probe anything over 600 mv and your generators is ok under replace
Posted on Feb 17, 2009
Make sure your thermostat can be used with a millivolt system.Most thermostats are for 24 volt systems and don't work for millivolt systems. Also your thermostat wiring cannot be too long and it also needs to be the correct gauge. Normally the thermostat wire size should be 18 AWG up to 50 feet in distance. Also all your wiring connection have to be clean and tight(solid connections). If your connections are the slightest bit loose your millivolts will drop.
Posted on Nov 11, 2009
Go to www.grainger.com and look for a "power pile generator" this is a millivolt thermocouple that may be just what you need to make your heater work again
Posted on Nov 12, 2009
SOURCE: I have a Pyromaster item
I am nearly 100% certain that your fireplace has the millivolt gas valve....
If it does not have a power cord going to it then I am sure it is millivolt...
Posted on Dec 30, 2010
Tips for a great answer:
Apr 05, 2013 | Imperial IFS-40 - Gas Deep Fryer - 40 Lb -...
Jul 09, 2012 | Imperial IFS40 Deep Fryer
Sep 20, 2011 | American Range AF-25 Deep Fryer
Jun 15, 2011 | Imperial IFS40 Deep Fryer
Apr 19, 2011 | Empire DV-35 Heater
Jan 23, 2011 | Teledyne Laars Laars Lite 2 Pool Heater...
Nov 19, 2009 | Pool & Spa
Oct 19, 2009 | Desa International Wall/Window Air...
Sep 04, 2009 | DCS FSF-40 Deep Fryer
93 people viewed this question
Usually answered in minutes!