Question about Electrical Supplies
I bought this generator a few years ago after experiencing a long power outage. Being a portable generator, it isn't the quietest. I'm afraid that if I start it up during the next power failure, my neighbors will complain. I wish there was a way to make it quieter. Any ideas?
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
If this is one of the big "taco cart" portables you need to check that the vent on the gas cap is open when you're running the engine. In the center of the gage on the gas cap is a little knurled knob, turn it counter clockwise (lefty loosey), about a half turn or so and run the generator.
If that doesn't solve your problem add to it here, otherwise please give me a rating I'm trying to build a little credibility here and could use the help.
Posted on Dec 02, 2008
First check the circuit breakers on the control/outlet panel.
Then take the end off the generator and look at the brushes (usually what breaks) and the 2 slip rings they ride on (these get dirty and have to be cleaned off with a bit of emery cloth)
Then look at the voltage regulator (the little board that the brushes plug into)
Let me know if you need more detailed help,
Posted on Dec 03, 2008
SOURCE: Generac Guardian 15kW Generator
That sounds just about right, if the relay contacts get welded together it sometimes takes out the driver on the printed circuit board. As you found out, 12vdc from 23 to 194 makes the transfer switch move to the Generator position, relay not energized makes the ATS move to the Normal position.
You can make a nice test function by installing a 10 amp contact switch in series with either the N1 or N2 terminals. When the switch is open the generator thinks the Normal power has failed.
Posted on Jan 26, 2009
SOURCE: 10kw Generac shut down overspeed
Make sure that the throttle linkage is all there and not damaged/misadjusted, then get a manometer and check your inlet gas pressure. Gas pressure should be 8 inches of water column and stay there running or not.
Posted on Apr 06, 2009
I am assuming the generator worked fine before the oil change. Now that you have done the oil change the genset does not start. These generators have a safety switch, which is basically an oil pressure switch that keeps the engine from running when there is not enough oil in the engine. Make sure that there is enough oil and if there is, look for a wire that runs along side of the engine to a round component. disconnect that wire and try starting. If it does not start then try to ground out the wire to the engine block. If this does not work, then there is other engine problems.
Posted on May 08, 2009
Tips for a great answer:
Jun 28, 2016 | Generac Electrical Supplies
Apr 18, 2016 | Generac Electrical Supplies
Dec 12, 2015 | Generac GUARDIAN Standby Generator 10 kW/9...
Nov 03, 2012 | Generac 5606 XP Series XP8000E 12,000 Watt...
Aug 10, 2011 | Generac Power Systems Generac QT02224 22...
Jul 25, 2010 | Generac Power Systems Generac 5525 20 Kw...
Sep 08, 2009 | Generac Guardian 100 Amp Transfer Switch...
Sep 04, 2009 | Generac Guardian 100 Amp Transfer Switch...
Jul 23, 2009 | Electrical Supplies
Nov 24, 2008 | Coleman Powermate Premium Plus 6250W...
Aug 18, 2017 | NEC Mitsubishi MGE 4000 Generator ROU...
17 people viewed this question
Usually answered in minutes!