Question about Carrier Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: My Heat will not work
the e2 code on a carrier comfort zone thermostat is indicitive of the external safety sensors which are located on your units ductwork in the attic. the e2 code are the hpt/ and lat sensor codes. the hpt is the heat pump temperature sensor and the lat is the leaving air temperature sensor. you can pull off the cover of the panel and behind it will actually give you all the fault codes associated with you carrier tsat.each sensor has a certain ohm rating and if its out of the range it will fail. now as to the reasons for failure, the indoor coil could be dirty, filters dirty, refrigerant charge incorrect.
Posted on Dec 22, 2008
the e2 error on your thermostat is a problem with the return temp sensor on your system, the only thing you can really do is call a company and replace it, you can't bypass it or remove it cause the system wont run properly
Posted on Jun 30, 2009
It means the trailer is too warm for the thermostat to work - above 90 degrees inside. Take some ice and put in ziplock bag - place over thermostat and cool it down. Unit will start working when thermostat senses it is BELOW 90 degrees. FAULTY DESIGN.
Posted on Jul 15, 2011
Tips for a great answer:
Mar 05, 2014 | Carrier Totaline P291-1003 Capacitor 10mfd...
Jul 06, 2011 | Dometic Rooftop RV Air Conditioner
Aug 13, 2010 | Goodman CLQ36AR49 Air Conditioner
Nov 22, 2009 | Carrier TSTATHCP Programmable Thermostat...
Jun 29, 2009 | Carrier 38CKC060 Air Conditioner
Jun 24, 2009 | Carrier 38CKC060 Air Conditioner
Jun 05, 2009 | Carrier 38CKC036 Air Conditioner
Dec 03, 2008 | Carrier Heating & Cooling
167 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: