Question about Leviton 3W Switch With U Grounding - 5245 - Brown
Switch is wired wrong.
But not sure how it's wired
Copy following link for wiring 5245 combo 3-way switch outlet.
Also look at illustration just below that shows no-neutral.
You replaced old 3-way switch.
Wire that connected to dark screw on old switch, connects to dark screw on 5245.
Wires that connected to other two screws on old switch, connect to 2 brass-colored screws on 5245.
Neutral wire must connect to silver screw on 5245.
Posted on Oct 29, 2012
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 14, 2016 | Electrical Supplies
May 08, 2014 | Electrical Supplies
Sep 25, 2017 | Cooper Industries Electrical Supplies
Nov 19, 2011 | Home
Apr 04, 2011 | Maytag Microwave Ovens
Feb 08, 2011 | Canon PowerShot A520 Digital Camera
Mar 01, 2010 | Leviton 5603-wh 3 Way Decora Switch
Mar 11, 2009 | Kenmore Refrigerators
Feb 18, 2009 | 1999 Chrysler Concorde
Jun 29, 2007 | Cannon i70 Printer
151 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: