Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
could be thermocuple or pilot blocked clean pilot then try make sure you are turning to on and not back to off i was doing this the other day some go clockwise some anticlockwise
Posted on Jan 02, 2010
Assuming the pilot is clean and sharp. Before replacing the valve, clean any spade connections, those going up to the spill switch in particular. Clean and tighten all 4 connections. Good luck.
Posted on Jan 11, 2010
The pilot flame must touch (burn) the tip oqef the t-couple to hold the magnet in the gas value open.make sure the pilot orifice (hole) is clear.the pilot pressure (in the tube) is factory set full open & can only be adjusted down (less). Also check the gas **** didn't get closed or turned half way.? Assuming its not the t-couple. If all is good & it still won't stay on. Replace the gas value.!
Posted on Sep 21, 2011
Tips for a great answer:
Dec 16, 2013 | Intertherm P3RA-048K Air Conditioner
Sep 14, 2012 | Heating & Cooling
Jan 13, 2012 | Heating & Cooling
Oct 29, 2010 | Heating & Cooling
The pilot light jet may have got a little bit of dirt or grit in it which is preventing it from keeping alight. Try probing the jet with a fine piece of wire to see it the blockage can be dislodged. You may have to unscrew the jet to clear it by blowing air through it. Make sure gas is turned off first before removing any parts.
The pilot light also has a thermocouple that allows gas to the pilot light while the flame is burning. If flame goes out it shuts gas off to the pilot jet. The thermocouple is bypassed by a switch during the initial ignition and once the thermocouple warms up after a minute or two of holding in the bypass switch, it should maintain the pilot. If, after cleaning, the pilot light keeps going out, it would seem that your thermocouple is faulty and needs to be replaced
Sep 27, 2010 | Intertherm Heating & Cooling
Jan 13, 2010 | Heating & Cooling
80 people viewed this question
Usually answered in minutes!