Question about Raypak Pool & Spa
Posted by Anonymous on
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
My Rapak gas pool heater burner will not ignite. I changed the flame sensor and then the main gas valve (on a recommendation of a heating contracter) and after spending almost $300 on parts, I may have not needed, it still will not ignite. The water temp has been around 80 using the solar cover but now with the air temp in the 50's at night and only in the 70's in the day the water is a brisk 70 degrees. We would like run the heater now, so we can use the pool for a bit longer this fall.
Any ideas? Some people told me there is a valve that senses the proper amount of water is flowing around the boiler so it doesn't burn up, is this possiblely the problem that the valve is not opening?
Joe Snyder, Toledo, Ohio
Posted on Sep 09, 2009
Thank you for posting your question here on Fixya.com.
Replacing the roll out switch is an easy do-it-yourself repair. Fixing the problem causing the roll out of the burner flames in the first place is a bit more of a pro job. Something is causing to much heat to roll out the the combustion chamber into the control area causing the switch to fail. You will continue to burn the link until the underlying problem is fixed.
If this answer does not fix your problem, please comment with additional details prior to rating the answer. Positive feedback is appreciated once your problem is solved!
Posted on Jun 01, 2010
SOURCE: service code ROL
This indicates the flame roll out safety switch is bad. This part is usually mounted right above the burner tray. It is a white ceramic piece with two wiring terminals and an external part that looks like a resistor. This part detects flame/heat coming out from the burner tray. When replacing it, be sure to check for blockage at the burner tray, heat exchanger and the flue if vented with duct work. This is a critical safety device so do not bypass it.
Posted on Jun 19, 2010
Tips for a great answer:
Oct 11, 2014 | Raypak 2100 Pool Heater Gas 266000 BTU'...
Aug 17, 2014 | Raypak 406A Digital ASME Natural Gas IID...
Oct 05, 2012 | Raypak Pool & Spa
May 11, 2012 | RAYPAK R406A DIGITAL MODEL 406 wCUPR0...
Oct 03, 2010 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
Aug 03, 2010 | Raypak Free Hydraulic Lift Gate Delivery -...
Jul 25, 2010 | Raypak 130,000 BTU Propane Gas Pool...
May 29, 2010 | Raypak 130,000 BTU Propane Gas Pool...
Sep 16, 2009 | Raypak Pool & Spa
Jul 06, 2009 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
185 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: