Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
There should be a set of metal cards attached inside the fireplace.
First you should read everything there.
I know you have to first light the pilot light.
And then there should be a wall switch.
The problem I have currently is that it won't stay lit when the artificial logs are there.
Posted on Nov 23, 2008
Gas apliances have safety features built into them so you don't blow yourself up. The pilot heats a thermocoupler which tells the gas valve there is a flame, open the main gas to the burner. If you can see the flame area of the pilot look for a round post about 3/16 inch in diamiter. This should be directly in the flame, if not bend the bracket so it is in one side of the pilot flame. The thermocouple is attached to a mounting bracket. This will be held in place by a 1/4 inch hex screw. remove the screw and the capilary tube leading to the gas control valve. Before you do anything, close the main gas supply to the fireplace and disconnect the power to the fan. You may need to semi dismantle the fireplace to get the thermocouple. The gas valve end is a brass 1/4 pipe thread plug. Turn the outer nut and remove without twisting the tube. Reverse this order to install a new one. Besure not to twist the capilary tube, tighten brass nut 1/4 turn past hand tight. Your better heating supply house will have these in stock. Restarting the pilot will take a few tries because the gas was off. Your gas suplier would charge about $75 to fix this. if you don't have the proper tools and it dosen't look pretty stright forward don't do it. You could get dead.
Posted on Dec 02, 2008
Hi , you can try and pull the panel on the bottom of fireplace out and check the adapter in fireplace. Sometimes they go bad. When you open in also check to see if there is an adapter plugged in and a option to use the battery operated function. If this goes bad the pilot will not stay lit.
Posted on Jan 14, 2009
Sometimes when you turn a gas heater off for some time, if the source tank has been turned off, the line will bleed the propane and the line will contain mostly air. This is especially true if the supply line is long. In order to light the pilot, you will have to hold the pilot lighting button down for a while (a full minute or longer, depending on the size and length of the supply line) before pure propane arrives at the pilot light jet. You should keep a lighted lighter at the jet so that when the gas arrives, the lighter will light it. After the pilot lights, you will have to keep the button pressed long enough for the thermocouple to get hot enough to set the pilot to stay on. When it is hot enough, you should be able to release the pressed lighting button and the pilot should stay on. If it does, you should be able to light the heater. If the pilot jet never lights, gas is not getting to the regulator. If the pilot will not stay lit after a period of time waiting for it to heat the thermocouple, the thermocouple or the regulator may be bad and need replacement. :-)
Posted on Jan 03, 2010
Ventless Gas logs, Vanguard, VS30PR. Propane gas
Pilot light stays lit various times, sometimes for several days then other times for a few minutes. Lights best when temp outside is below freezing. Pilot flame appears to receive too much air. How do you adjust the pilot flame? Is this done using two screws marked A & E? Do you have suggestions?
Posted on Jan 08, 2010
Tips for a great answer:
Jan 06, 2017 | Majestic Heating & Cooling
Dec 11, 2016 | Kitchen Ranges
Oct 10, 2013 | Majestic Fireplaces Majestic Topaz 20ILDV...
Nov 06, 2012 | Heating & Cooling
Dec 02, 2010 | Heating & Cooling
Nov 09, 2010 | Heating & Cooling
Jan 07, 2010 | Napoleon 36" Zero Clearance Top/Rear Vent...
Nov 13, 2009 | Napoleon 36" Zero Clearance Top/Rear Vent...
Nov 04, 2009 | Leisure HOMEPRIDE Electric Fireplace...
Sep 20, 2017 | Heating & Cooling
105 people viewed this question
Usually answered in minutes!