Question about Dayton Heating & Cooling
I push in the pilot button, hit the sparker and the pilot light stays lit until I release the pilot light button and then the pilot light goes out
Posted by Anonymous on
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Unable To Keep Pilot Light Lit!
I have a Williams top vent gravity wall furnace (model 5009622) and I had the same problem. I had to take the cover off the furnace -- screw on top and two at the bottom (open the access door and there is one screw on each side) to get to the reset button for the vent safety shutoff system. On my furnace it's on the left side toward the top of the unit. I pressed the little red reset button and it's been working ever since. If your furnace is properly installed and doesn't have bird's nest in the chimney, it should work fine. Good luck!
Posted on Dec 06, 2007
Gas apliances have safety features built into them so you don't blow yourself up. The pilot heats a thermocoupler which tells the gas valve there is a flame, open the main gas to the burner. If you can see the flame area of the pilot look for a round post about 3/16 inch in diamiter. This should be directly in the flame, if not bend the bracket so it is in one side of the pilot flame. The thermocouple is attached to a mounting bracket. This will be held in place by a 1/4 inch hex screw. remove the screw and the capilary tube leading to the gas control valve. Before you do anything, close the main gas supply to the fireplace and disconnect the power to the fan. You may need to semi dismantle the fireplace to get the thermocouple. The gas valve end is a brass 1/4 pipe thread plug. Turn the outer nut and remove without twisting the tube. Reverse this order to install a new one. Besure not to twist the capilary tube, tighten brass nut 1/4 turn past hand tight. Your better heating supply house will have these in stock. Restarting the pilot will take a few tries because the gas was off. Your gas suplier would charge about $75 to fix this. if you don't have the proper tools and it dosen't look pretty stright forward don't do it. You could get dead.
Posted on Dec 02, 2008
SOURCE: pilot light will not stay lit
Clean the pliot light tube with a Q-Tip and alcohol. Clean 2 inches deep. This will increase the pilot light flame and it will heat up the thermocoupler so it will stay lit.
Posted on Dec 06, 2008
Hi , you can try and pull the panel on the bottom of fireplace out and check the adapter in fireplace. Sometimes they go bad. When you open in also check to see if there is an adapter plugged in and a option to use the battery operated function. If this goes bad the pilot will not stay lit.
Posted on Jan 14, 2009
SOURCE: Pilot light won't stay lit
Look for dust and lint. Look for them in places where gas should be freely flowing. I had a similar problem with an Empire Corcho wall-mounted propane ceramic catalyst heater. First it was the pilot light, then the #2 ceramic mantle. After horsing around with the gas lines and pressure regulators and trying to re-aim the pilot, it all turned out to be dust and lint in the gas passages. A little dust bunny in the brass pilot tube gave me a pilot light the shape and color of a banana. One puff of compressed air, and I got back my razor-sharp pilot. And some dust in the chimney of the #2 burner kept it burning blue/yellow and blistering paint off the upper surfaces of the heater. A bit of cleaning with a shop-vac put that right. "Passive" heaters are very much prone to this sort of problem because they rely on convection currents (i.e. LOW velocity) to get the job done. Convection currents are notorious dust collectors, as in COBWEB CITY.
Posted on Feb 28, 2009
Tips for a great answer:
Dec 15, 2015 | Fisher Paykel Fisher & Paykel 24-in...
Nov 26, 2013 | Woodland Direct CD Vent Free Gas Log Set...
Oct 28, 2012 | Heating & Cooling
Feb 14, 2010 | Endless Summer (GA200209) Stainless Steel...
Nov 13, 2009 | Napoleon 36" Zero Clearance Top/Rear Vent...
Oct 19, 2009 | Heating & Cooling
Oct 13, 2009 | Desa International Heating & Cooling
Jun 24, 2009 | Hayward 250kbtu Ng Pool Heater - Inground
Apr 05, 2009 | Heating & Cooling
Jan 13, 2018 | Dayton Heating & Cooling
76 people viewed this question
Usually answered in minutes!