Question about Heating & Cooling
Pilot lights but once blower turns on, pilot goes off.
I have the same furnace. Major recall on heat exchangers. contact coleman at 888-665-4640 to see if you qualify for the recall. You will need your serial number when you call.
Posted on Oct 30, 2013
Heat exchanger could well be split causing it to blow out pilot
Posted on Oct 27, 2012
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
I am not familiar with this heater but it sounds like it could be a blockage in the main gas line into the heater or perhaps a blockage to the pilot gas line and maybe starving for gas. Best bet first is to check the main gas line from the heater. Easiest way to do this is to remove it from the heater and blow it through with compressed air. Then try the heater again. If that doesn't fix the problem then you can try blowing compressed air down through the pilot line. Could be a little dirt creating a blockage there. Then try the heater again. If it still does the same thing then try removing the panels to expose the heater's piping. If you can remove the main pipe into the heater from the gas and blow compressed air through it it should clear any obstruction from both the main line and the pilot. If this doesn't work then I would think you have a more severe problem and will need to take it to your local Heater Repairer. Hope this helps.
Posted on Dec 22, 2007
Make sure all the wire connections are good and tight. Next lift off the cover and look for a little thermal disc mounted up by top of the heat exchanger. Most have a re-set button but not all. If you have this ,by-pass it ,see if that solves the problem, if so it may be defective, or doing its job and you have a venting problem. If you don't have this and have changed the thermocouple (was it a copper tube with a fitting that screwed into the gas valve, or did it have 2 wires, that is a pilot generator, kind of same thing) make sure the probe is set correct, with the pilot flame heating the top 1/3rd of the probe. The only thing left is the gas valve.
Posted on Dec 25, 2007
SOURCE: cozy furnace
The pilot orifice could be dirty causing the pilot flame to be too small. Unscrew the pilot tube at the pilot assembly. The orifice is inside. Remove the orifice and blow it out with compressed air only. Reassemble and see if that fixes the problem. If the pilot flame is set too low, sometimes opening a door will cause a draft to blow out the pilot. If the thermocouple is good and the pilot flame is set properly, the control valve may be bad.
Posted on Feb 05, 2009
Go to www.grainger.com and look for a "power pile generator" this is a millivolt thermocouple that may be just what you need to make your heater work again
Posted on Nov 12, 2009
Tips for a great answer:
Oct 02, 2015 | Coleman Gas Fired Mobile Home Furnace,...
Oct 21, 2013 | Omega Trane Furnace Draft Inducer Blower...
Oct 15, 2013 | Heating & Cooling
Jan 15, 2011 | Coleman Heating & Cooling
Dec 13, 2009 | Tools & Hardware - Others
Dec 03, 2009 | Heating & Cooling
Oct 08, 2009 | Heating & Cooling
Jan 17, 2009 | Coleman Propane Forced Air Heater...
Nov 22, 2008 | Heating & Cooling
Sep 17, 2008 | Coleman Heating & Cooling
Aug 21, 2017 | Heating & Cooling
332 people viewed this question
Usually answered in minutes!