Question about LG LSC121PMA Split System Air Conditioner
Outside unit will not start,fan will spin if you kick start so it seems to be a cap. at fault? the start up caps. seems to be part of pcb,can these be changed or is it a new board? fan for outside unit when spinning is very slow,runs 20 mins then c6 again.. can i check voltage to compressor,or windings resistance. any help on this would be great,thanks phil.
Condenser fan windings are rooted. No capacitor due to multi speed. Replace condenser fan motor they just clip on pcb.
Posted on Feb 08, 2011
Try turning the power off at the fuse box, waiting 5 minutes turning the system back on and spray some water on the vents on the side of the outside condenser. If the fan isnt spining get a twig and spin it in an anti-clockwise direction after 1 or 2 spins it should start spinning on its own. continue to hose the vents with water for another 5 minutes. Its important to have the fan spinning as it extracts the heat from the condenser box.
Posted on Jan 31, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 25, 2013 | LG LAN186HV / LAU186HV 18,000 BTU 15 SEER...
Dec 13, 2010 | LG Art Cool LA121HNP Split System Air...
Aug 19, 2009 | Carrier 38CKC042 Air Conditioner
Feb 28, 2009 | LG Art Cool LA121HNP Split System Air...
Jan 02, 2008 | Heating & Cooling
Sep 08, 2007 | LG Art Cool LA121CNP wall/window Air...
960 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: