Question about Intertherm 56000 Btu Gas Furnace
If the sensor knocks the unit off and the the fan keeps blowing without a flame ,the limit (the sensor is a limit comptroller that turns off flame @ a set temp and allows the fan to run until the heat exchanger cools to @ set temp) has out lived its lifetime and needs to be replaced.the button is a manual reset that once reset would allow the unit to continue to run flame and blower at the same time after having been set once, if it is an ongoing problem and needs to be reset more than once then replace the limit control (sensor) in kind. (With the same mode and set-points for the limits)
Posted on May 30, 2014
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 13, 2014 | Heating & Cooling
Jun 05, 2017 | Heating & Cooling
Oct 25, 2012 | Intertherm 56000 Btu Gas Furnace
Dec 20, 2010 | Heating & Cooling
Nov 19, 2010 | Heating & Cooling
Jan 24, 2010 | Heating & Cooling
Jun 09, 2009 | Coleman Propane Forced Air Heater...
Feb 21, 2009 | Goodman CPLE24-1 Air Conditioner
Jan 08, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Oct 28, 2008 | Goodman GMS90703BXA Heater
Sep 26, 2017 | Honeywell Heating & Cooling
139 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: