Question about Goodman CLQ36AR49 Air Conditioner
I was reading that to use a Audible Ohmeter to a Capacitor on a fan motor. I have a regular Ohmeter can I use it and how?
Watch out for those caps.you use the ohms setting ,may have to go to higher setting in ohms,but take your probes place on cap terms.the cap will read closed for a few seconds then go open,then reverse the probes and do again same result.if only open then may be bad,if your meters reading fine.i have only ever used a regular meter in all the years gone by.God bless,tom
Posted on Jan 02, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 08, 2012 | LG LW7000R Air Conditioner
Oct 01, 2011 | Ruud UBHC Air Conditioner
Jun 18, 2011 | Heating & Cooling
Oct 12, 2010 | Hayward Pool Products Hayward Power Flo LX...
Sep 18, 2010 | Pentair Pinnacle 1 1/2 - Hp In Ground Pool...
Sep 05, 2010 | Hampton Bay HBLG5004 Air Conditioner
Sep 08, 2009 | Vornado Air Circulator - Black
Aug 19, 2009 | Heating & Cooling
Aug 13, 2009 | Mitsubishi Mr. Slim MXZ30TN Air...
Mar 10, 2009 | Heating & Cooling
281 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: