Question about Procom ML300TBA Heater
I have tried different hoses, conectors and regulator to avail. the pilot lite barely has a flame, will not lite enough to get flame for the heater
Not enough information to solve the problem correctly but I'll take a guess at it......
This heater requires a 100lb propane tank (approx. 25gal) with 1/2" or larger piping to deliver the correct volume of gas to the heater. If you are using a smaller tank (like a 10gal) or the piping is not the correct size you will not get enough gas to the heater to light the pilot. Also you should have a regulator set at 11" to 14" of water column installed between the tank and the heater. If the tank is connected directly to the heater you may have damaged the internal regulator in the heater.
Posted on Feb 18, 2009
Blocked pilot injector clean out pilot should work then
Posted on Jan 02, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 07, 2011 | Coleman Heating & Cooling
Jan 31, 2011 | Vanguard Heating & Cooling
Nov 07, 2010 | Uniflame 200209 Open Flame Patio Heater
Sep 04, 2010 | Williams 2509612 Ceramic Mid-Size Heater
Jan 13, 2010 | Dyna-Glo (PPH16-LP) Utility Heater
Jul 04, 2009 | Endless Summer 2009 Open Flame Patio...
Feb 15, 2009 | Mr. Heater Mr Heater Portable Buddy...
Jan 16, 2009 | Heating & Cooling
Nov 20, 2008 | Reddy Heater RLP100 Portable Forced Air...
246 people viewed this question
Usually answered in minutes!