Question about Heating & Cooling
Pull the fuses and check voltage line to line with the fuses out you should have 208 to 240 volts if you have 50 or so volts try line to ground if you have 120 on one leg it will back feed with the fuses in,because of the windings involved. in any case you are missing one leg somewhere to get the voltage readings that you have poasted
Posted on Jan 11, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 30, 2011 | Heating & Cooling
Feb 09, 2010 | Dometic Rooftop RV Air Conditioner
Nov 25, 2009 | Heating & Cooling
Nov 24, 2009 | Heating & Cooling
Oct 29, 2009 | Heating & Cooling
Jun 21, 2009 | Honeywell Programmable Thermostat Heater
Apr 05, 2009 | Carrier 38BRC048 Air Conditioner
Jan 11, 2009 | Heating & Cooling
Sep 26, 2008 | Goodman Heating & Cooling
74 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: