Question about Carrier XHB123D X/Y Series Heat/Cool Air Conditioner
Unit kicks on as described and the main gas valve kicks-on and ignites and stays on for about 30 to 445 seconds and then goes out. Honeywell trouble-shooting chart says it may be a grounding problem of the igniter or excessive heat at Q 34 which causes short to ground. I can make it work by reducing Temp below room Temp for 60 + sec and leave fan in ON position then increase Thermostat above room temp. However, once it goes off it will return to lockout condition. Sounds like bad S86A Intermittent Pilot Gas Burner ignition System. Anyone agree? If so, where are parts available?
I hate to admit it but this is a common problem with the Honeywell S86A control. If you can find a heating slpy house neat you that sells to the public your lucky, more than likely you will have to get it from a heating company. a carrier/bryant/payne/day&night (all made by carrier) should have one on hand.
Posted on Jan 02, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 02, 2015 | Hayward H Series Electronic Ignition...
Feb 28, 2013 | Amana Dryers
Mar 30, 2011 | Dayton (3E405) Gas Radiator Heater
PROBLEM #1 - HOT SURFACE IGNITOR DOES NOT GLOW RED
(Remember to wait for purge time, 17/34 seconds, on models so equipped).
A. No main power
B. Faulty transformer
C. Faulty thermostat
D. Faulty limit switch
E. Faulty blower interlock switch
F. Faulty hot surface ignitor
G. Faulty ignition control
Perform normal system checks of main power, transformer, thermostat, limit
switch, blower interlock switch, and replace faulty component.
With power on and thermostat set at its highest position, check voltage
between "TH" and "TR" on HS780 ignition control. If 24 volts is not present
check output at transformer. If no, replace transformer. If transformer
checks out OK look at other controls in the 24 volt circuit I.E.: thermostat,
limit switch, blower interlock switch. Check for 120 volts between "neut"
(L2) and "120" (L1). Check for 120 volts at the ignitor across "IGN" and
"IGN" terminals on the HS780 ignition module. If 120 volts is present,
replace ignitor. If no, replace the 780 series module
PROBLEM #2 - IGNITOR GLOWS RED BUT MAIN BURNER
A. Improper ignitor alignment
B. Faulty ignition control
C. Faulty gas valve
D. High inlet gas pressure
E. Polarity reversed
F. No earth ground
Check for availability of gas at gas valve. Make sure the manual valve
upstream of the gas valve and the gas valve are in the full on position. Also
make sure gas is being supplied to the system at the proper pressure, too
high will lock-up the valve.
Check proper polarity of "NEUT" and "120" on the ignition control by reversing
the wires, if reversed gas valve will not open. If this does not solve the
problem, replace wires as they were.
Check for proper ignitor position.
Check for a good earth ground by using a meter connected between L1
and furnace chassis. Should read 120 volts, if no, check and/or repair ignition
ground wire or ignition control mounting screws.
CAUTION POLARITY MUST BE OBSERVED
Check for 24 volts at the gas valve terminals; "1" and "2" on a 7200 series,
"M" and "C" on a 7100 series, "TH" and "TR" on a 7000 series. If yes,
check wire integrity or change the gas valve. If no, change the 780 series
That is pretty much all of the troubleshooting required.
Thanks for choosing FixYa,
Feb 14, 2011 | Rheem 40 Gallon FVR NATGAS Low WATER...
Feb 01, 2011 | Bosch 425HN NG Tankless Water Heater
Aug 03, 2010 | Kenmore Dryers
Feb 20, 2010 | York Furnace Draft Inducer Blower Fasco #...
Oct 24, 2009 | Rheem 50 Gallon FVR NATGAS Water Heater...
Jul 03, 2009 | Heating & Cooling
Jan 07, 2009 | Heating & Cooling
84 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: