Question about Ruud Matching Split Air Conditioner
The central heating light flashes continually and although the hot water and central heating light go on nothing happens. If I reset the central heating temperature control by switching off and then positioning I get hot water for 4 mins before it reverts back to flashing. What's the problem? How can it be fixed? I've had for about 4 years and no problems until now.
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: worcester bosch highflow 400
Sounds like a control panel.Detatch the block connector that serves the gas valve,see if you have power on the bare pins.both left and right pins should measure mains voltage.If you have no power at the pins its the pcb control board.Replace the board.
Posted on Nov 24, 2008
It sounds the furnace is going into lock out, you have a safety fault problem of some kind.
It could a ignitor, flame sensor, limit or roll out switch, etc.
You really need to have a service technician check it out.
Posted on Mar 26, 2010
Tips for a great answer:
Dec 31, 2017 | Heating & Cooling
Feb 09, 2016 | Water Water Heaters
Dec 07, 2013 | Bosch Water Heaters
Jan 19, 2013 | Bosch Worcester Spark Electrode...
May 13, 2010 | Bosch Water Heaters
Nov 06, 2009 | Ruud Matching Split Air Conditioner
May 18, 2009 | Water Heaters
Nov 23, 2008 | Ruud Matching Split Air Conditioner
Nov 01, 2008 | Heating & Cooling
1,001 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: