Question about Rinnai RHFE-1004FA 38,400 BTU Energy Saver Ductless Heater - LP Gas
We recently had a Rinnai 1004FA installed. We lost our propane furnace to flooding & now the Rinaai is our main heat source. Because times have been tough, we started out with the "economy" setting, and the propane level on our tanks were 70% when it was installed.
9 days later, our propane tanks were at 30 %!!!!!!!!!!!!
I immediatly called the propane CO, who sent out a repairman to check for a leak.
He promptly told us that when you set it to "economy", it NEVER shuts off!
So much for "energy saving"!
Anyway, he removed the side panel & raised the thermistor to just above the top of the unit.
We thought PROBLEM SOLVED
Umm, not quite!
For the past 3 days, I have it set to 60
Even after reaching the 60 degrees, it will NOT shut off.
It runs CONSTANTLY!!
If I set it to the "low" setting, (55-58 degrees), it will shut off, obviously because the room was just at 60, but min later, on it goes again!
No matter what temp I set it at, it doesn't shut off when it reaches the set temp.
I am totally stressing myself out as to what my next propane bill will be.
I CANNOT afford another $300 bill every 2 weeks :(
Test the thermistor by using an ice cube. Place the cube on the thermistor and see if the unit starts. Then using a warm towel, wrap the thermistor ans see if it stops. Watch the display to see if it is registering the changes in temp. I suspect a bad thermistor.
Posted on Jan 05, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 25, 2011 | Rinnai RHFE-1004FA 38,400 BTU Energy Saver...
Jun 05, 2011 | Rinnai RHFE-1004FA 38,400 BTU Energy Saver...
Feb 15, 2010 | Rinnai RHFE-1004FA 38,400 BTU Energy Saver...
Jan 13, 2010 | Rinnai Heating & Cooling
Dec 16, 2009 | Rinnai RHFE-1004FA 38,400 BTU Energy Saver...
Sep 11, 2009 | Rinnai RHFE-1004FA 38,400 BTU Energy Saver...
Aug 25, 2009 | Rinnai RHFE-1004FA 38,400 BTU Energy Saver...
Nov 23, 2008 | Rinnai RHFE-1004FA 38,400 BTU Energy Saver...
Oct 12, 2008 | Rinnai RHFE-1004FA 38,400 BTU Energy Saver...
508 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: