Question about Fujitsu 24R1 Air Conditioner
Our split system airconditioner has started leaking water from the condenser (opposite side to the outlet pipe) into the house. Filters are clean. The drain to the outside appears to be clear.
Is there any way that it would have realigned itself on the wall?
Either the drain line is clogged, or there is a hole in the pan.
Get a powerfull wet/dry shop vacume.
Attatch it to the end of the drain pipe and seal it tight and pull out any dirt, mold crud blockages.
Take the panel off so you can access the drain pan under the evap coil. Clean that out as well with the vac.
Once its nice and clean, poor a gallon or so of water into the pan bein g carefull to not pour to fast.
Make sure that the line is drainign well and look for any spots where there may be a crack, hole etc in the drain pan where water may leak out
Posted on Jan 01, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 15, 2011 | Heating & Cooling
Oct 14, 2010 | Oldsmobile Alero Cars & Trucks
Sep 09, 2010 | 2003 Pontiac Sunfire
Aug 26, 2010 | LG Heating & Cooling
Aug 25, 2010 | AmcorAire UCHW-H12AF2 Split System Air...
Jun 02, 2010 | Coleman Mach 15 Air Conditioner
May 19, 2010 | GE Zoneline AZ38H12DAD Split System Air...
Jan 20, 2010 | Dishwashers
Nov 16, 2009 | GE Zoneline AZ38H12DAD Split System Air...
Aug 15, 2009 | Heating & Cooling
795 people viewed this question
Usually answered in minutes!