Question about Fujitsu 24R1 Air Conditioner
Our split system airconditioner has started leaking water from the condenser (opposite side to the outlet pipe) into the house. Filters are clean. The drain to the outside appears to be clear.
Is there any way that it would have realigned itself on the wall?
Either the drain line is clogged, or there is a hole in the pan.
Get a powerfull wet/dry shop vacume.
Attatch it to the end of the drain pipe and seal it tight and pull out any dirt, mold crud blockages.
Take the panel off so you can access the drain pan under the evap coil. Clean that out as well with the vac.
Once its nice and clean, poor a gallon or so of water into the pan bein g carefull to not pour to fast.
Make sure that the line is drainign well and look for any spots where there may be a crack, hole etc in the drain pan where water may leak out
Posted on Jan 01, 2009
Tips for a great answer:
Mar 15, 2011 | Air Conditioners
Aug 25, 2010 | AmcorAire UCHW-H12AF2 Split System Air...
May 19, 2010 | GE Zoneline AZ38H12DAD Split System Air...
Nov 16, 2009 | GE Zoneline AZ38H12DAD Split System Air...
Aug 15, 2009 | Air Conditioners
Aug 03, 2009 | GE Quiet-Aire Ductless Split System Air...
Feb 23, 2009 | Cfm Daikin R410a Split System Air...
Jan 05, 2009 | LG LS-L1210CL Mini Split Air Conditioner
Dec 30, 2008 | Fujitsu 24C1 Air Conditioner
779 people viewed this question
Usually answered in minutes!